The guy that came out was not the first these guys are great at what they do they got me a great price and looking forward to getting unit put in
Great service thanks again!
Reece came to our home and thoroughly checked everything out for us. He explained what was going on and went over all options. He has great customer service skills, patient, and very punctual.
All around great experience from the first step in the door to the final step at the end.
No heat winder. Completed diagnostic. Thermostat just needed to be reset. Reset thermostat. System turned off and came back on appropriately. Checked system. Air flow is good coil is clean. Blower wheel is slightly dirty. System has no back up water safety or air purification. Recommend inline float switch to protect system and home from water damage. As wel as electro static filter and UV light system to better filter air and kill any bacteria and viruses in air to keep system clean and residents healthy. Outdoor unit running good. Recommend hard start kit to assist compressor with start up which will extend life of compressor and lower energy bills.
Free consultation for mini split in garage winder Georgia 30680
No heat in winder. Arrived on site, found upstairs zone thermostat has gone bad and is not sending signal back to zone board in heat mode. Replaced with Honeywell T4 and tested system. Unit is operating normally at this time. I recommend installing secondary water safty switch and surge protector to protect electrical systems in furnace.
Furnace diagnosis in Winder, Georgia. Tested system and found it operational. Found blower capacitor to be very weak, recommend replacing. Customer wants to replace himself. System is heating at this time.
Ac diagnostic in Winder, Georgia. Found system with very dirty filter, changed filter. Found blower capacitor to be extremely weak (10uf). Found dual capacitor to be weak. Found system very low on r22. R22 is a refrigerant that has been phased out by the epa. System needs to be replaced.
No cool in winder . Arrived on site, found outdoor control wire going to unit cut, repaired wire and tested system. No other issues present at this time.
Ac diagnostic in Winder, Georgia. Tested system and found no issues. System is cooling at this time.
Completed diagnostic. Found one year old system with terminals unplugged from compressor. Plugged back. Got system running. Amps are good on compressor and fan. Pressures are good. Feta T inside house is good. System cooling at this time. Customer declined maintenance plan for now.
System has weak compressor. 410a 3 ton condenser was installed on a 2 ton r22 coil. Compressor not pumping at capacity. System needs to be replaced
One system tune up. Customer says zones are not keeping up. Tested system. Zone dampers are functioning properly. Found evaporator coil slightly dirty. Found air leakage where unit connects to supply plenum. Added tape to better seal airflow. Recommend sealing with mastic. Found weak capacitor and system is overcharged. Recommend replacement of capacitor and adjusting refrigerant pressures. Recommend cleaning of evaporator coil. Return ductwork is undersized by 300 cfm, recommend installing another 10â€ return for proper airflow. Supply ductwork is undersized by 120 cfm, recommend installing another 8â€ duct with damper for improved airflow. System is cooling at this time.
No cool, found bad capacitor, replaced under full warranty. System is cooling at this time.
A/c repair call. Found system with a bad capacitor (45/5 uf). Found dirty blower wheel as well. Water safety on the system is code compliant but there is no overflow protection switch for the drain line. Recommend replacing the capacitor, cleaning the blower wheel, installing overflow protection switch, and installing a hard start kit to reduce the load on the compressor so it starts smoother, runs smoother, and therefore lasts longer. Replaced capacitor. The system is cooling at this time. Thank you so much for your business today!
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Completed one system maintenance found blower and evap coil clean. Changed filter cleared drain line. System has no air purification other than standard one in filter. Would benefit from having UV air purifier and electro static filter to better filter air and keep system and house cleaner longer. Outdoor system has good pressures and working electrical components. System has no compressor saver or surge protection
Completed one system tune up found system 13 years old and running on r22 refrigerant. Informed customer of phase out of r22. Indoor system zoned has no back up water safety installed. Blower whee is clean filter is good. Outdoor unit does have good pressures and has working electrical components. System is cooling properly at this time.