They came toward the beginning of the time window, fixed the problem quickly and were very knowledgeable. Would highly recommend!
It was nice that Roger was able to come to our home on a Saturday morning and give us a quote. Very informative and honest. Good job, Roger
performed heating maintenance on Goodman and trane heat pump AC split system
Complete: 1System EPA Maintenance Came to finish maintenance at AH. Checked amp draws on the motor and the heat strips. Checked blower bearings. Evap looks good. All looks good and working great at this time.
Incomplete: 1 System: Amana Split HP: EPA Maintenance: checked filter inside. HP: Checked charge, Amp draws on fan and compressor and checked capacitor. Cleaned electrical panel. Went to the AH and they recently put new siding on their home. The siding comes down and blocks door from opening. Could not get access to AH. The HO wife asked us to call to reschedule second half of maintenance once access is clear. Condenser may still need to be washed.
Replaced a fan control board on a Payne air handler
Replaced blower motor on a Lennox heat pump
replaced indoor coil on Lennox heat pump AC split system zoned
Incomplete: 2 Systems worked on downstairs Unit: Lennox split HP: HO said wasn’t cooling the way they desired and heard motor rev-ing up and down over and over. At AH found motor doing just that boy in heat mode and cool mode. Checked and had 120v going to motor. Checked speed tap number one with 24v jumper and motor would rev up and down. Need new x13 blower motor
Leak searching a Lennox heat pump
Replacing an evaporator coil on a Goodman air handler
Maintenance on a Lennox heat pump
Routine maintenance on an Amana heat pump