They came toward the beginning of the time window, fixed the problem quickly and were very knowledgeable. Would highly recommend!
It was nice that Roger was able to come to our home on a Saturday morning and give us a quote. Very informative and honest. Good job, Roger
Complete: 2 systems worked on US system Heil Split HP: HO said was cooling great and suddenly stopped cooling. At the HP found bad 30/3 cap. Had to add dual 30/5 and a 3mfd run. Checked charge and system is running great at this time.
Complete two systems, worked on downstairs unit, Goodman split heat pump. Found 10 mfd bad in crawl space. System is operating properly at this time.
Complete 2 systems worked on DS Unit Goodman split HP: HO said stopped cooling. Found 10mfd bad in crawl space also found couch pushed up against return. Checked vents and had 54° coming out and temp dropped 3° while I was there. SH was at 27°. System is working great at this time.
Incomplete: 1 system Bryant split HP: HO had a representative there for her. He said it was out of refrigerant. So I went to the HP and sure enough it was bone dry.
Complete two systems, Goodman heat pumps, worked on upstairs unit. Found bad dual capacitor and replaced it. Also changed p-trap. System is operating properly at this time.
Complete: Came to replace Tstat and EIM. Replaced rewired and setup Tstat. System is operating as it should at this time. The Tstat Kit came with an EIM so we can return the other we purchased.
American standard ac check
Goodman ac check
Replacing a blower motor on a Nordyne electric furnace
Working on a Bryant gas pack
Goodman and train heat pump cooling maintenance
Complete: 2 systems worked on DS Unit: Trane Split HP: HO said wasn’t cooling any longer. Found HP not working checked under the house and found condensate pump had gfi tripped due to clogged line. Unclogged line and reset gfi and system came on. Condensate pump is working. System is working as well.
Complete: 2 Systems worked on US Unit: Trane split HP: When we arrived HO said the system wasn’t blowing cold air and that the breaker was tripped. At the HP found dead compressor
Working on a Goodman heat pump
Complete: 2 System: EPA Maintenance Goodman Split Heat Pump: US Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this Time.