They came toward the beginning of the time window, fixed the problem quickly and were very knowledgeable. Would highly recommend!
It was nice that Roger was able to come to our home on a Saturday morning and give us a quote. Very informative and honest. Good job, Roger
Complete: Worked on Upstairs Unit. Complete: 2 Systems: Carrier Split HP: HO Said unit leaking water. Found water leaking out from around bathroom vent. (Pics in Docs). At the AH found pan full of water and leaking out of secondary drain plug. Plug is not ran outside just stopped capped off. Checked condensate line and secondary line. Both clean and clear replaced P-Trap and secondary pan plug. Found no sign of leaking in primary pan. At the HP found system low in refrigerant. Believe the water in pan was due to unit freezing and thawing out. Added 1lb of 410 and checked to make sure Unit was draining properly. Informed HO with findings and system looks good and working great at this
replaced x13 blower motor on carrier heat pump AC split system
Worked on a Goodman heat pump replaced weak capacitor
Working on a Carrier heat pump
Complete: 1 (2) zone System: HO said HP was making loud noise. At HP found fan not running, check fan cap and it’s was low. Replaced cap and it still struggled to come on. Tried bigger cap due to motor being able to use it. Same result. Looked and saw that the motor had two wires hanging on the inside. It was actually a plug that had come unplugged. Plugged them in, went back with the smaller 7.5 cap and system fired up. Checked charge and amp draws, RA and SA and system is working great at this time!
Sold new comfort system with enhanced air filtration.
Replacing an evaporator coil on a Heil heat pump
Performed leak search on ICP heat pump
Complete: 1 System: Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Repaired thermostat wire on Goodman heat pump.
Replaced contactor on Goodman heat pump
Working on a Goodman heat pump
Working on a Goodman package heat pump
Goodman Package Unit, Bad Compressor Plug, Changed it out, working great!
Performed diagnostic on Payne gas pack