They came toward the beginning of the time window, fixed the problem quickly and were very knowledgeable. Would highly recommend!
It was nice that Roger was able to come to our home on a Saturday morning and give us a quote. Very informative and honest. Good job, Roger
Replacing a blower motor on a Nordyne electric furnace
Working on a Bryant gas pack
Goodman and train heat pump cooling maintenance
Complete: 2 systems worked on DS Unit: Trane Split HP: HO said wasn’t cooling any longer. Found HP not working checked under the house and found condensate pump had gfi tripped due to clogged line. Unclogged line and reset gfi and system came on. Condensate pump is working. System is working as well.
Complete: 2 Systems worked on US Unit: Trane split HP: When we arrived HO said the system wasn’t blowing cold air and that the breaker was tripped. At the HP found dead compressor
Working on a Goodman heat pump
Complete: 2 System: EPA Maintenance Goodman Split Heat Pump: US Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this Time.
Complete: 2 systems worked on DS Unit Goodman split HP came to replace fan and motor on condenser. Replaced both checked charge and system is working great at this time.
Complete: 1 System: $99 Maintenance Heil Split Heat Pump: Air Handler: Checked Thermostat and Filters and Amp Draws on the Blower Motor, Inspected Evap coil. checked condensate line and pump Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Complete: 2 systems worked on US Unit: HO said outside fan wouldn’t work. Found fan locked up. Replaced with truck stock 2spd 1/6hp Rescue motor. Checked charge and system is working great at this time. Also sold Two system maintenance. Need to schedule TU ASAP.
Working on a Goodman heat pump
Complete: 2 systems worked on DS unit: Goodman split HP: Came to replace compressor. Removed warranty compressor (pics in Docs) flushed system and added acid remover. Added new filter and new compressor. Nitrogen, bubble tested. Pulled vacuum and added 7lbs of 438 refrigerant. Had and 18degree delta T and system called for a 12degree SH and I had 17. System is working as it should at this time.
Found restriction in piston and dirty coil
Complete: 2 Systems Worked on main floor unit: Payne Split HP: TN said unit wasn’t blowing much air. At HP Found unit 410a low side 37 and high side 280. Reversed flow of refrigerant and pressures went too 115 and 320. Did that a couple of times and the non-Adjustable TXV inside isn’t allowing refrigerant through. Needs new TXV.
Complete: 1System Goodman split Hp: HO said just stopped working. Found condensate pump cut power to HP due to gfi breaker trip in garage bc of stopped up tubing. Blew tubing out, reset gfi. System came on. Checked charge and system is working great at this time.