Joshua and Elmer were very efficient and professional with their work. They are a great asset to your company.
Complete 2 Systems worked on US Goodman HP Split System. Replaced compressor. Recovered ref. Removed old compressor. Replaced filter dryer. Had to repipe compressor. Replaced dual cap. Replaced core valves. Leak tested system. Pulled vacuum. Added 8 lbs of R22. Checked pressures. System is running great at this time.
Working on a Goodman heat pump
Rheem Heat pump package unit replaced condenser fan motor
Trane equipment no issues
Complete: 1System Rheem Package Unit. HO said unit just suddenly stopped blowing cold air. I found the outdoor portion locked up. Cap was reading good but burning hot. Changed cap and system fired up. Bad dual cap. Changed cap and system is working ok. Pressures were still kind of weird but blowing great cold air. Age of system I told HO he is def on borrowed time.
Goodman gas package unit cooling maintenance
Apollo furnace cooling tune up
Carrier split straight a.c. cooling tune up
Trane split heat pump. Repaired wire on condenser fan motor
Rheem heatpump inspection
Amana split straight AC, diagnosed leaking txv metering device
Carrier Split system straight AC cooling maintenance
Trane diagnosed bad compressor
Goodman split straight AC diagnosed leaking service valve