Goodman equipment......cooling tune up
Complete: EPA Maintenance: Goodman Package Unit: Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Checked condensate line. And washed Coils. Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Carrier split heatpump replaced warranty compressor
Goodman split heat pump. Sealed blower doors
Goodman split heat pump cooling maintenance
Trane split heat pump cooling maintenance
Amana split heat pump cooling maintenance
Epa maintenance on 1 amana heatpump split system and 1 goodman split system heatpump.
Rheem heat pump found capacitor bad replaced added hard start to lower amp draw on start up
EPA maintenance on an Amana heat pump system
EPA maintenance on a Trane heat pump system
Rheem heat pump package unit heating maintenance
York Heat Pump
Carrier Heat Pump.