Trane ac,system check
Nordye EPA maintenance
Diagnosed a bad compressor on a rheem heat pump
Diagnosed speaking system on a trane package unit
Worked on trane heat pump and zoning -checked refrigerant charge-
Carrier gas furnace checked system found blower motor not running due to bad contral board and replaced and cycled system working at this time
Trane A/C replaced zone dampers
Found bad capacitor not turning unit on
Cooling maintenance on straight ac
Found leak on system, repairs by braising hole. System cooling properly at this time.
Rheem split heat pump. Replaced bad outdoor txv causing unit not to heat
Comfort maker split heat pump. Found leaking condenser coil
Goodman Package Unit: HO said would not come on. Checked power at the unit and breaker was tripped. Ohmed out the compressor and Compressor is grounded. Needs new compressor.
Goodman package heat pump, found low voltage wiring issues and corrected