Trane split heat pump. Replaced bad tstat with new and replaced bad hard start with new
Carrier 80% gas furnace heating tune up
Payne gas furnace heating tune up
Carrier gas furnace heating tune up
Carrier mini split replaced bad dual cap
Trane gas furnace heating tune up
Payne gas pack heating tune up
Lennox mini split system. Replaced bad compressor with new and recharged system
Goodman package heat pump. Replaced burned up blower motor, blower wheel, capacitor, and heat kit. Checked system for proper operation
Goodman heatpump package replaced heat kit,blower motor, blower wheel and capacitor.
Carrier split heat pump. Diagnosed leaking evaporator coil
Complete 1 System Trane HP Split System. Performed Heating Maintenance Checked thermostat and air filter. Checked amp draws on heat strips and blower motor. Inspected evap coil. Made sure drain line was clear. Checked all wiring. Checked compressor and cfm amp draws. Tested defrost board. Checked dual cap. Checked pressures. Checked all wiring at condenser. Cleaned condenser coil. System is running great at this time.
Complete: Worked on DS Rheem HP: Replaced 15’ of 16” return duct. Attached to plenum and added collar to connect two pieces of duct. Also noticed band holding return side of system had broken causing unit to not be level. Strapped it back up as well as duct. Cleaned out condensate Ptrap and blew out line. Outside dug down to condensate drain coming out of foundation wall and added an elbow and piped down grade to allow better drainage. Everything looks good and working great at this time.
HP Split System: Checked Air Filters and thermostat. Checked amp draws in blower motor, inspected evap coil. Made sure drain line was clear. Checked all wiring at AH. Checked amp draws in compressor and CFM, checked dual cap. Checked pressures. Checked reversing valve. Cleaned condenser. Tested defrost board. Checked all wiring at condenser. System is running great at this time
Complete one system, split heat pump, two zones. Found blown 5 amp fuse in air handler and replaced it. System is operating properly at this time.