I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Fantastic job - quick and efficient, careful and kind. Gave me good info on how to use systems properly. Very professional.
Cody and partner were very great. Explained my options and even offered maintenance. Upstairs is cool, wife is cool so all good!
Great job. Done quickly.
Repaired a carrier gas furnace by replacing the evaporator coil and recharged system
Carrier A/C checked system found bad dual run capacitor and hard start and replaced and cycled system working at this time
Repaired a York gas pack by cleaning the coil
Repairing Carrier Heat Pump
Maintenance Downstairs Unit: Carrier Gas Pack Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Changed condensate line. And washed Coils. Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Carrier air handler and zone system replaced zone damper motor and cycled system working at this time
Comfortmaker gas furnace replaced 2 pis low pressure gas regulator in gas line near furnace
Working on carrier heat pump drain line
Repaired a Lennox heat pump by replacing the evaporator coil
Working on a Goodman heat pump
Working on a Goodman heat
Working on a carrier heat pump
Working on a trane heat pump
Installing a new amana split heat pump heating and cooling system
We installed a 2 ton straight ac an conventional system downstairs and a 3 ton ac system,with 80% furnace upstairs , also added a 6" supply in bonus room ,