We highly recommend Comfort First as we have been customers for many years via their maintenance agreement. Today, we had the pleasure of meeting with Bill Smart regarding the purchase/installation of a new unit. His professionalism, customer service and honesty was beyond measure. We will continue our service agreement with Comfort First because they give us peace of mind.
Joel and his team were professional and courteous. Install was smooth. Install passed inspection the very next day.
Thomas and his team were great! We called American Home Shield when our AC failed in August on a Sunday. We got a call from Comfort First Heating and Cooling Monday morning that they would be out Monday afternoon, fine with us considering we didn’t make the initial call until Sunday afternoon. Thomas and his team actually came earlier which was a nice surprise. They diagnosed the problem quickly and had us back up and running within an hour. I highly recommend Comfort First Heating and Cooling and in particular Thomas!
Joel was extremely knowledgeable and professional. A pleasure to work with. Thoroughly explained the entire process. I would HIGHLY recommend him and his team!!
Very pleased with the professional work performed by the team
Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
He was great at explaining everything, answered all my questions.
I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Incomplete: 2 systems worked On DS Trane Gas Pack. Changed out board and high limit switch. Turned unit on and the inducer wouldn’t come on. Checked voltage and inducer had 240 going to it but the motor would not come on. Also board was throwing bad pressure switch code. Jumped it just in case but not going to make a difference if inducer isn’t running.
Replaced compressor carrier ac
Ducane package unit
Estimate for new heating and cooling system
Working on a Carrier A/C
Lennox furnace check
Nordyne ac check
Lennox hp check
Routine maintenance on 2 Carrier furnaces
Rheem gas pack check
Tempstar furnace check
Performed heating maintenance training split heat pump
Lennox hp check
Complete 1 System Amana HP Split Systems. Came to perform EPA Heating Maintenance Checked Air Filters and thermostat. Checked amp draws in blower motor and heat strips. Inspected evap coil. Made sure drain line was clear. Checked all wiring at AH. Checked amp draws in compressor and CFM, checked dual cap. Checked pressures. Tested defrost board. Cleaned condenser. Checked reversing valve, Checked all wiring at condenser. System is running great at this time.