Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
He was great at explaining everything, answered all my questions.
I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Fantastic job - quick and efficient, careful and kind. Gave me good info on how to use systems properly. Very professional.
Cody and partner were very great. Explained my options and even offered maintenance. Upstairs is cool, wife is cool so all good!
Great job. Done quickly.
CARRIER gas furnace checked duct work
CARRIER gas furnace found wires on board touching causing heat and a/c to run at same time
Lennox heat pump bad txv
Incomplete: 2 systems worked on downstairs unit: Goodman AC Gas Furnace. HO said it was not blowing air. At the Gas Furnace found the inducer motor locked up. Need to order new inducer from East Coast
CARRIER gas furnace bad inducer motor and high limit
Carrier Gas Pack found bad control Board need to order
Trane split Heat Pump changed Heat Kit
Concord heat pump bad compressor
Trane heat pump split system found bad capacitor
Goodman gas pack found someone has been working on system mis wired bad board
Goodman package heat pump found evaporator coil iced and thermostat locked out with a code customer doesn't know code
CARRIER gas pack bad capacitor
Dual fuel replaced board
Trane gas pack found bad inducer motor
Rheem gas furnace replaced hot surface igniter