I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Fantastic job - quick and efficient, careful and kind. Gave me good info on how to use systems properly. Very professional.
Cody and partner were very great. Explained my options and even offered maintenance. Upstairs is cool, wife is cool so all good!
Great job. Done quickly.
Carrier straight a.c.. Checked unit for proper operation
Carrier straight a.c. with gas furnace. Found unit low on r410a.
Cleared clogged drain line
Clogged drain and hole in secondary pan
Rheem gas pack bad collector box
Goodman ACS insufficient coolant
Goodman ac......blown 35/capacitor
Clogged drain cleared
Trane low in refrigerant R410-A
Trane gas furnace low voltage short
Serviced Carrier Gas package unit,found bad capacitor & hard start.repaired both checked operation.great at this time.
Noise coming from second floor unit blower motor
Carrier AC second floor 7.5 capacitor blown condenser fan motor
Goodman gas pack checked system found bad dual run capacitor and replaced