I was very happy with the work that Tyler did. He was very courteous and respectful. He even got to know my dog. He even brought her a treat the second day on the job.
Thank you for the follow-up to adjust the airflow!
We highly recommend Comfort First as we have been customers for many years via their maintenance agreement. Today, we had the pleasure of meeting with Bill Smart regarding the purchase/installation of a new unit. His professionalism, customer service and honesty was beyond measure. We will continue our service agreement with Comfort First because they give us peace of mind.
Joel and his team were professional and courteous. Install was smooth. Install passed inspection the very next day.
Thomas and his team were great! We called American Home Shield when our AC failed in August on a Sunday. We got a call from Comfort First Heating and Cooling Monday morning that they would be out Monday afternoon, fine with us considering we didn’t make the initial call until Sunday afternoon. Thomas and his team actually came earlier which was a nice surprise. They diagnosed the problem quickly and had us back up and running within an hour. I highly recommend Comfort First Heating and Cooling and in particular Thomas!
Joel was extremely knowledgeable and professional. A pleasure to work with. Thoroughly explained the entire process. I would HIGHLY recommend him and his team!!
Very pleased with the professional work performed by the team
Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
Rheem gaspack no ac
Rheem gaspack running constantly
Carrier A/C checked system found very dirty condenser coil and cleaned also found systems to be low in refrigerate need to add 2 lb R-22 refrigerate
Carrie gas furnace preformed leak search
Carrier gas furnace replace condenser fan motor
Carrier gas furnace furnace replaced condenser fan motor
Goodman gas furnace found bad compressor
Lennox gas furnace found bad dual run capacitor
Carrier gas furnace replace door run capacitor
Carrier blown capacitor
Rheem hp......replaced cfm blade
Rheem ac no cooling
Complete 1 System Carrier Straight A/C: HO stated outdoor unit was not running and making a loud noise. Found bad cfm. Used 1/4HP 240V cfm. P#:1860. Truck stock. Replaced it. Checked pressures. System is running great st this time.
Complete 3 Systems worked on A Goodman Straight A/C for basement HO stated system was not cooling. Found bad dual cap. Used a 35/5 cap from truck stock. C hecked pressures. System is running great at this time.
Incomplete 1 System Lennox HP Split System 3 Zones. HO stated zone for 2nd floor was not working. Cycled system. Zone damper motor for 2nd floor was not opening. Checked to make sure mother board and tstat were working as they should. They are working properly. Motor damper for 2nd floor is bad. Not opening. Tried to find it but we couldnt. Flexes from supply plenum lead to the attic but we didnt find any access to the attic. There were 3 access doors at the 3rd floor on the wall, we opened them up but didnt have any flexes with motor dampers. Tried 2nd floor. We didnt find any thing. HO said he will find with recent owners and then will call us back. 2nd floor zone still not working.