We highly recommend Comfort First as we have been customers for many years via their maintenance agreement. Today, we had the pleasure of meeting with Bill Smart regarding the purchase/installation of a new unit. His professionalism, customer service and honesty was beyond measure. We will continue our service agreement with Comfort First because they give us peace of mind.
Joel and his team were professional and courteous. Install was smooth. Install passed inspection the very next day.
Thomas and his team were great! We called American Home Shield when our AC failed in August on a Sunday. We got a call from Comfort First Heating and Cooling Monday morning that they would be out Monday afternoon, fine with us considering we didn’t make the initial call until Sunday afternoon. Thomas and his team actually came earlier which was a nice surprise. They diagnosed the problem quickly and had us back up and running within an hour. I highly recommend Comfort First Heating and Cooling and in particular Thomas!
Joel was extremely knowledgeable and professional. A pleasure to work with. Thoroughly explained the entire process. I would HIGHLY recommend him and his team!!
Very pleased with the professional work performed by the team
Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
He was great at explaining everything, answered all my questions.
I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Amana split heatpump preformed cooling maintenance
Trane furnace check
Lennox furnace check
Lennox Package Unit
Carrier Gas Package Unit
Carrier gas pack check
Lennox cooling maintenance
Amana split heat pump performed cooling maintenance
Amana hp check
Goodman ac check
Amana furnace check
Carrier furnace repair
Carrier ac check
Complete 1 System Came to perform EPA Cooling Maintenance. HO Stated System last year finished summer season great. Checked thermostat and replace air filter. Checked run cap. Checked blower motor amp draws. Checked blower wheel and all wiring at AH. Inspected evap coil and made sure drain line was clear. Cleaned condenser coil. Checked compressor and cfm amp draws. Checked dual run cap. Checked pressures. Checked contactor coil resistance. System is running great at this time. $0 Collected