Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
He was great at explaining everything, answered all my questions.
I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Fantastic job - quick and efficient, careful and kind. Gave me good info on how to use systems properly. Very professional.
Cody and partner were very great. Explained my options and even offered maintenance. Upstairs is cool, wife is cool so all good!
Great job. Done quickly.
Incomplete: 1 System: 2 Zone Lennox Split HP: HO said that the system wasn’t heating but blowing out air. At the HP found refrigerant levels to be exactly where they need to be for a 410 system and amp draws and all doing what they should be doing. It’s 33 degrees outside and HP is working as it should. Emergency heat US is on but it’s only a 5kw Heat Kit. This system is a 2T system in a 2k sqft home. HO said that several neighbors had expressed similar issues with undersized systems. HO would like an estimate for either and upgrade or if a larger Heat Kit would make a difference. He does have vivant tstats on the wall. HO would like to speak with someone ASAP about giving him options and potentially running a load calculation on the home.
Complete: 2 systems: worked on DS unit: Goodman Gas Furnace: HO said Unit would come on and go rt back off. At furnace found glow plug not working. Had 120v getting to it. Replaced with new glow plug and unit fired up. Cycled system and unit is working great at this time.
Goodman gas package unit Diagnosed bad gas valve
Installed 3 ton Amana gas package unit with nest gen 3 thermostat
Lennox gas furnace found bad control board
Goodman gas furnace found bad inducer motor
Goodman gas furnace. Replaced broken hot surface igniter
Carrier gas package unit Replaced cracked heat exchanger
Trane gas furnace found bad pressure switch
Goodman gas furnace found bad inducer motor and pressure motor
Trane gas pack is found bad pressure switch
Carrier gas package unit Diagnosed bad control board
Lennox gas package unit. Replaced collapsed return ductwork