I was very happy with the work that Tyler did. He was very courteous and respectful. He even got to know my dog. He even brought her a treat the second day on the job.
Thank you for the follow-up to adjust the airflow!
We highly recommend Comfort First as we have been customers for many years via their maintenance agreement. Today, we had the pleasure of meeting with Bill Smart regarding the purchase/installation of a new unit. His professionalism, customer service and honesty was beyond measure. We will continue our service agreement with Comfort First because they give us peace of mind.
Joel and his team were professional and courteous. Install was smooth. Install passed inspection the very next day.
Thomas and his team were great! We called American Home Shield when our AC failed in August on a Sunday. We got a call from Comfort First Heating and Cooling Monday morning that they would be out Monday afternoon, fine with us considering we didn’t make the initial call until Sunday afternoon. Thomas and his team actually came earlier which was a nice surprise. They diagnosed the problem quickly and had us back up and running within an hour. I highly recommend Comfort First Heating and Cooling and in particular Thomas!
Joel was extremely knowledgeable and professional. A pleasure to work with. Thoroughly explained the entire process. I would HIGHLY recommend him and his team!!
Very pleased with the professional work performed by the team
Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
Installed split heat pump and complete duct system
Working on 3 Trane A/C systems
Working on a Carrier A/C
Working on a Carrier heat pump
Carrier A/C checked system found bad CFM need to replace CFM
Goodman A/C checked system found bad dual run capacitor and to be completely out of refrigerate and preferred leak search and found leaking condenser coil need to replace condenser coil
Rheem A/C replaced CFM and cycled system working at this time
Rheem no ac...ants contactor
Goodman ac...low charge
Air conditioning replacement
Carrier ac replace compressor
Goodman ac.....insufficient cooling
Complete 2 Systems worked on Both Systems US and DS. US Carrier Straight A/C: HO stated system was freezing up. Found system low in refrigerant. HO authorized ro add refrigerant. Added 2 lbs of R22 and a can of leak stop. Checked pressures. System is running great at this time. DS Carrier Gas Pak Straight A/C: HO stated that he just wanted his ds system checked out and make sure is was running properly. Cycled system. Monitored blower motor, compressor and cfm. Checked pressures. System is running great at this time.
Installed new furnace and outdoor unit