Billy did an excellent job, quickly identified the issue and fixed it. Would definitely recommend him to others
Heil equipment cooling maintenance
Complete 1 System Lennox 80% Gas Furnace. AHS Heating Maintenance: cycled system. Checked tstat and air filter. Checked electrical connections. Checked blower motor amp draw and run cap. Inspected evap coil. . Burners are clean. Inspected pilot. Checked amparage on draft motor and run cap. All safety switches are on great condition. Checked draft motor. System is running great at this time.
Worked on Carrier heat pump
York hp..low charge
Lennox gas pack.. No heat..
Repair on a Goodman air conditioning system
Goodman A/C bad capacitor
Rheem evaporator coil
Goodman ac refrigerant
Lenox second floor drain pan full of water as a result of primary Line stop
Replace Goodman gas pack blower motor
Bad Zone damper
Lenox heat pump one elbow R22
Lennoxe gas pack checked system found open pressure switch due to stopped up vacuum line and clear and cycled system working at this time
Repaired a trane gas furnace by cleaning flame sensor