The guys were excellent in their work & very polite. They took care in their approach in & around our home. I highly recommend them.
3.5 ton package unit and duct system
Complete 2 Systems worked on US Goodman HP Split System. Came to add 1 lbs of R22, to add a can of leak stop and install a new hard start kit. Added 1 lbs of R22, installed new hard star kit, and added a can of leak stop. Checked pressures system is running great at this time.
Complete 2 System worked on DS Goodman HP Split System. Replace defrost board and installed new hard start kit. System is running great at this time.
Carrier replaced cfm
Goodman heat pump checked system found compressor and condenser fan motor not running due to bad dual run capacitor and replaced and cycled system working at this time collected 0
Carrier heat pump checked duct work found to be ok at this time
ICP gas pack replaced gas valve and contral board and cycled system working at this time
Amanna ac and carrier ac completed cooling maintenance
Armstrong gas pack replaced draft inducer assembly and cycled system working at this time
Lennox A/C replaced ignition control board due to blower motor not running and cycled system working at this time