Outcome was not what we expected, but the rep was courteous and informative.
Jeffrey wqs outstanding in his work and his professionalism. I was very please with his quick response.
Incomplete: 1System Trane split HP: HO said system tripped breaker twice last week. I found system starting up fine. When I reset breaker to start again found compressor over amping with 30LRA. Needs new compressor. Called jimmy and we will not charge for refrigerant need to bring virgin recovery tank when we come to replace compressor.
Trane replaced start cap and relay
Complete: 1System Amana Split HP: HO said unit just didn’t seem to be keeping up. 1. He had the Nest learning features on the Tstat. So I removed all that. 2. His SH and SC was 14 and 7 but only a 14° drop. Adjusted txv and added 8oz of 410 and gained a 8° SH and 8° SC with a 19° drop. Tstat satisfied at 67°. Explained all my findings to mr Godwin and system is working great at this time.
American standard heatpump inspection
2.5 tons heat pump Goodman
Rheem gaspack no heat
Trane Split heat pump. Found bad condenser fan motor.
Complete 2 System 1 Amana and 1 Carrier HP Split Systems. Came to perform Heating Maintenance Right Carrier HP Split System: Checked Air Filters and thermostat. Checked blower motor and heat strips amp draws. Checked run cap. Inspected evap coil. Made sure drain line was clear. Checked all wiring at AH. Checked compressor and CFM amp draws. checked dual cap. Checked pressures. Tested defrost board. Cleaned condenser. Checked all wiring at condenser. System is running great at this time. Left Amana HP Split System: Checked Air Filters and thermostat. Checked blower motor and heat strips amp draws. Inspected evap coil. Made sure drain line was clear. Checked all wiring at AH. Called BJ to get settings right for best thermostat. Checked compressor and CFM amp draws. checked dual cap. Checked pressures. Tested defrost board. Cleaned condenser. Checked all wiring at condenser. System is running great at this time.
Replaced outdoor ambient sensor on Ruud split heat pump
Complete: 2 systems worked on DS Goodman Gas Pack: HO said system wouldn’t come on although the Tstat was saying it was on. She would literally push the reset button on her Tstat and it would come on. It wwould satisfy and she later would come back and turn it on and system wouldn’t come on and she would then reset it again. Everything system wise was working how it was supposed to. After cycling several times. Replaced Tstat with pro select tstat. Cycled system and is working great at this time.
Servicing air conditioning system heat pump
Trane split heat pump. Replaced bad compressor and recharged system
Goodman gas furnace replaced blower motor and capacitor found bad blower wheel part ordered
Found motor brok motor bracket on Goodman gas furnace
Bad blower motor on goodman split system straight ac