Jeffrey wqs outstanding in his work and his professionalism. I was very please with his quick response.
We installed a new 16 seer heat pump with 3 ton coil and mobile home furnace. Also ran new tstat wire to nest tstat and out door unit
Goodman heat pump checked system found to be working and maintaining temperature at this time
Goodman split heat pump. Found a broked blower wheel causing the unit to make a loud noise. Replaced broken wheel and ensured proper operation
Goodman split heat pump. Found and repair burned wires, a failed dual capacitor, and a bad defrost control board keeping the unit from running
Goodman heat pump. Restored voltage to unit
Working on package heat pump and zone board
Two Rheem heat pumps not working. Diagnosed fire ants causing a/c problem
System not cooling. Replaced bad capacitor. System cooling fine at this time.
Replacing evaporator coil
Found system blowing but not cooling. Found outside unit not running. Found outside unit locked-out on high pressure. Reset control board, ran system. Found system over-charged on Freon, adjusted. System has likely been locked-out since before switching to cooling mode. As a result, customer’s met next power bill may be high from overuse of aux heat in heating mode. System operating fine at this time.