Outcome was not what we expected, but the rep was courteous and informative.
Jeffrey wqs outstanding in his work and his professionalism. I was very please with his quick response.
Goodman gas furnace replaced blower motor and capacitor found bad blower wheel part ordered
Found motor brok motor bracket on Goodman gas furnace
Bad blower motor on goodman split system straight ac
York sp.it heat pump. Rep?ACED BAD DRAIN LINE float switch and replaced bad air handler breaker. Cheched for proper operAtion.
Goodman split heat pump. Replaced bad contactor and duel capacitor. Diagnosed compressor over amping on start up
Goodman split heat pump. Replaced leaking evap coil and recharged system
Comfort maker straight a.c.. Added hard start to help compressor
Goodman split heat pump. Replaced bad blower relay board
Trane split heat pump. Replaced faulty defrost board and condenser fan motor
Bryant split heat pump. Replaced bad contactor
Amana gas package unit Adjusted burners
Rheem gas package unit cooling maintenance
Carrier straight a.c. cooling maintenance
Carrier gas package unit cooling maintenance
Trane split heat pump. Replaced bad breaker