Jeremy and Cody were efficient, friendly and professional. They explained everything to me clearly and precise. Very pleased with the job and time spent on putting in the unit. They were not too long and did not put it in too quickly. Very pleased with their work.
Billy was an outstanding technician with a wealth of knowledge and a wonderful personality. I would recommend his service to anyone.
Quick, on time, professional and my equipment is back up running. Thanks.
Goodman A/C checked system found to be low in refrigerant and preferred leak search and found leaking condenser coil need to replace condenser coil
Goodman equipment Coil Frozen lost operation
Rheem heat pump checked system found to be working and maintaining temperature at this time
Bryant ac checked system found to be low in refrigerant and added 1 lb R-22 and cycled system working at this time
Ameristar heat pump checked system found blown 30 amp fuse and replaced and cycled system working at this time
Repaired a comfortmaker gas furnace by replacing the gas valve
Repaired 2 Goodman heat pumps by rewiring the tstat wires
Goodman gas pack replaced draft inducer assembly and cycled system working at this time
Found a stopped up air filter on a maytag gas furnace
Diagnosed a bad inducer assy on a Goodman gas pack
Installing nest thermostat with rheem outdoor heat pump and indoor system
3.5 ton heat pump install