Billy was excellent. Fully explained every step of the service process.
Jeremy and Cody were efficient, friendly and professional. They explained everything to me clearly and precise. Very pleased with the job and time spent on putting in the unit. They were not too long and did not put it in too quickly. Very pleased with their work.
Billy was an outstanding technician with a wealth of knowledge and a wonderful personality. I would recommend his service to anyone.
Quick, on time, professional and my equipment is back up running. Thanks.
Complete upstairs heat pump. Found bad contactor and capacitor and replaced them. System is operating properly at this time.
Work on Goodman air conditioner
Complete one system, worked on first floor system. Found bad capacitor and replaced. System is operating properly at this time.
Worked on Rheem air conditioner
Trane split heat pump. Replaced bad thermostat
Worked on Trane heat pump
Goodman a/c checked system found to be low in refrigerant and added 2 lb R-22 to system and cycled system working at this time
Goodman A/C checked system found to be low in refrigerant and added 1 lb R-22 and cycled system working at this time
Goodman an york low charge bad fuse
Goodman hp check