Jeremy and Cody were efficient, friendly and professional. They explained everything to me clearly and precise. Very pleased with the job and time spent on putting in the unit. They were not too long and did not put it in too quickly. Very pleased with their work.
Billy was an outstanding technician with a wealth of knowledge and a wonderful personality. I would recommend his service to anyone.
Quick, on time, professional and my equipment is back up running. Thanks.
Repaired a trane heat pump by adding a hard start
Repaired a trane heat pump by replacing the condensate pump
Goodman checked system found condenser fan blade shredded due to being out of balance need to replace CFB
Goodman A/C checked system found low suction and low high side pressure due to restriction at piston at evap coil and replaced piston and pulled vacuum and added 2 lb R-22 to system and cycled system working at this time
Diagnosed a leaking evaporator coil on a Goodman heat pump
Goodman AC units not cooling
Trane ac pump
Carrier gas pack Place control board
Goodman A/C checked system found to be low in refrigerant and preferred leak search and found leaking condenser coil need to replace condenser coil
Goodman equipment Coil Frozen lost operation
Rheem heat pump checked system found to be working and maintaining temperature at this time
Bryant ac checked system found to be low in refrigerant and added 1 lb R-22 and cycled system working at this time