Jeremy and Cody were efficient, friendly and professional. They explained everything to me clearly and precise. Very pleased with the job and time spent on putting in the unit. They were not too long and did not put it in too quickly. Very pleased with their work.
Billy was an outstanding technician with a wealth of knowledge and a wonderful personality. I would recommend his service to anyone.
Quick, on time, professional and my equipment is back up running. Thanks.
Trane heat pump checked system found to be working and maintaining temperature at this time
Goodman package heat pump checked system found 2 blown 30 amp fuses and replaced and cycled system working at this time
Goodman hp....no cooling
Cooling tune up
Goodman furnace bad inducer motor
Carrier Furnace blowing 3 amp fuse short in the outdoor unit
Rheem equipment question about Nest Thermostat
Goodman air handler checked duct work a d found be intact with no issues
Complete: 1 System: Goodman Package Unit: HO said was making a loud noise. Found metering device chattering and system low in 410a. Added a 1 lb. Pressures rose up piston quieted down. System went into defrost pressure looked normal in cool mode. Heat strips are working. System looks good and working great at this time.
Rheem and Ducane heat pumps completed EPA heating maintenance and cycled system working at this time
Repaired a trane heat pump by adding a hard start
Repaired a trane heat pump by replacing the condensate pump
Goodman checked system found condenser fan blade shredded due to being out of balance need to replace CFB
Goodman A/C checked system found low suction and low high side pressure due to restriction at piston at evap coil and replaced piston and pulled vacuum and added 2 lb R-22 to system and cycled system working at this time