I am very pleased with Ben, the service tech. He is friendly, courteous and I was pleased with his attention to detail during the service.
Great service getting the HVAC system running the way it is supposed to be.
Tech's, replaced indoor and outside coils under warranty...curteous, informative, and demonstrated excellent knowledge during service call!
The techs arrived and were friendly and well mannered. They got to work right away and identified the issue quickly. They also identified a mistake from the original installation and corrected it. It was an overall wonderful experience.
Company offered to place us on priority list due to infant in the home on mechanical support for breathing. Crew on time and friendly, worked quickly to assess problem and make repairs. Repair covered under homeowner's insurance, no cost to us as renters. Highly recommend.
Complete: 1System: Came to replace OEM Fan Motor and CAP. David M said he had already changed the CAP and turned in Warranty CAP to warehouse. So I’m bringing new one back. Replaced Fan motor and cycled system. Working great at this time!
2 system Goodman heat pump cooling maintenance
Train split heat pump no cooling
1 System low on refrigerant Added 4 pounds of 410A Freon
Miller split heatpump no cooling
2 System EPA cooling maintenance Heat pump/air handler
Goodman split heat pump maintenance
Found bad zone control board on Westinghouse split heat pump
Completed cooling maintenance on Goodman split heat pump
Completed cooling maintenance on Trane split heat pumps
Complete: 1 System: EPA Maintenance Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Completed cooling maintenance on Trane split heat pump
Completed cooling maintenance on Goodman gas pack
Found bad blower motor on Goodman split heat pump
Found bad tsat on heil split heat pump chains g system to heat on cool mode