Awesome service, timely, and professional
I am very pleased with Ben, the service tech. He is friendly, courteous and I was pleased with his attention to detail during the service.
Great service getting the HVAC system running the way it is supposed to be.
Tech's, replaced indoor and outside coils under warranty...curteous, informative, and demonstrated excellent knowledge during service call!
The techs arrived and were friendly and well mannered. They got to work right away and identified the issue quickly. They also identified a mistake from the original installation and corrected it. It was an overall wonderful experience.
Company offered to place us on priority list due to infant in the home on mechanical support for breathing. Crew on time and friendly, worked quickly to assess problem and make repairs. Repair covered under homeowner's insurance, no cost to us as renters. Highly recommend.
Trane heat pump heating maintenance
Wiring repair on a Nordyne heat pump
Carrier split heat pump heating maintenance
Trane split heat pump maintance
Complete one system, whole house. Preformed heating maintenance checked amp, blower motor, compressor, condenser motor, capacitor, refrigerant, and cleaned coils. System is operating properly at this time.
Complete one system, Trane heat pump. Preformed heating maintenance, cleaned coils, checked charge, parts, amp draws, and heat kit. System is operating properly at this time.
Working on a Goodman heat pump
Working on a Hell hear pump
Complete: 2 systems worked On US unit. Goodman split HP. TN said outside unit stopped working The at the HP contactor stopped up with Death by suicide ants. Anyway, I cleaned the ants out of contactor and best I could out of electrical cabinet. System is working great at this time.
Completed two systems, upstairs Goodman split heat pump. Found AH condensate line clogged, replaced p-trap and blew out line. System operating properly at this time.
Complete 2 systems worked on US Unit Goodman split HP: HO said unit was cutting off and he noticed water in his drain pan. Found AH condensate line clogged ...... replaced Ptrap and blew out line and resealed with insulation. HO is interested in 2 system EPA Maintenance. I told him all about it and thinks he will call in to sign up. Also he is wanting a primary float switch. He said he would call in about that as well. System is working as it should at this time.
replaced contactor on Trane heat pump split unit AC
Repairing air conditioning system
Checking a Nordyne heat pump