Worked on Goodman heat pump check unit found bad capacitor installed new 45 + 7.5 microfarad capacitor Cycle System running properly
Worked on Goodman heat pump cleared clogged drain line replace P-trap cycled system running properly
Worked on Trane heat pump Replace defective thermostat Cycle System running properly
Replaced capacitor and added refrigerant to HVAC system.
Comfortmaker ac checked system found to be low in refrigerant and added 2 lb R-22
Replaced a compressor