Great personalities, very knowledgeable and extremely helpful
Extremely knowledgeable and professional gentlemen. Cody, Joel, and Marco got right to work and ensured the system was functioning at 100% before they left. They also gave extra care to our home and family. Finally, they ensured we were left in a position to fully utilize the new systems and all of its capabilities. Thanks, guys!
The service was second to none. Bought the system and it was installed within 24 hours and everyone from Comfort First was very professional. An outstanding company
Called to have someone diagnose and fix a small issue that I had with my system. Their techs knew exactly what it was and wasted no time getting me up and running. The expertise and professionalism provided by their experts is second to none.
Technician was very personable, knowledgable and patient to address all of our questions and concerns. He led us to make a well-informed decision in our purchase of needed equipment. GREAT JOB!
Technician was thorough and explained his diagnosis with possible solutions which may solve the problem.
Renee was very professional and friendly, she made the experience very easy and comfortable, since this was the first time I had to do this! The accuracy and timely manner things were taken care of just BLEW me away!!! I would definitely recommend this company and Renee to ANYBODY needing a heating/cooling system!
Really nice wholesome gentleman
Goodman heat pump with mortex AH cooling maintenance
Working on a Heil heat pump
2.5 ruud heat pump
Working on a Goodman heat pump
Leak testing a Goodman heat pump
Replacing an evaporator coil on a Heil heat pump
Routine maintenance on an Amana heat pump
Amana split heatpump preformed cooling maintenance
Working on a Nordyne heat pump
Replacing a compressor on a Intertherm heat pump
Working on a Carrier heat pump
complete two systems, worked on DS unit. Thermostat was not responding. Pulled thermostat and found extra wire causing the thermostat not to set base correctly. Recharged thermostat. Rewired t-stat. Placed nest t-stat back on the wall and all is working great at this time. Didnt need to use new t-stat. Bringing it back in tomorrow.
Complete: 1System 2zone Westing House SplitHP: HO said wasn’t cooling. At the HP found system extremely low in refrigerant. At the AH found Capacitor low. Informed HO of the issues. The unit holds 17lbs of refrigerant. Told her we would need to do a leak search and replace the capacitor. She asked how much for all. Once I told her the total cost of refrigerant She said she looked online and found it for $10 a pound. She said thank you but no thank you. So I collected the service fee and left.
Goodman split heat pump no heat
Goodman split heat pump maintenance