Comfort First AC has been servicing and repairing my units for the past 8 years. The are always prompt and resolve the issue quickly. During this time, the followed all PPE requirements due to the pandemic. Highly recommended this company.
Bradley McLeod was excellent. He was on time and knew what needed to be done.
Had a duo come to the house. Anthony and Bradley stopped by on my original call about the AC being inop. It sorted itself out (extremely hot when I made the call) before they arrived. They had no problem checking up on the system to ensure it is running the way it should. Recommend the maintenance program.
Took time and care by offering the various options available, the problems that needed to be addressed, and the work to be done.
Great personalities, very knowledgeable and extremely helpful
Extremely knowledgeable and professional gentlemen. Cody, Joel, and Marco got right to work and ensured the system was functioning at 100% before they left. They also gave extra care to our home and family. Finally, they ensured we were left in a position to fully utilize the new systems and all of its capabilities. Thanks, guys!
The service was second to none. Bought the system and it was installed within 24 hours and everyone from Comfort First was very professional. An outstanding company
Called to have someone diagnose and fix a small issue that I had with my system. Their techs knew exactly what it was and wasted no time getting me up and running. The expertise and professionalism provided by their experts is second to none.
Complete: HO said smelled kind of putrid coming from US system. We checked out the AH in the attic and everything looked fine HVAC wise however we did smell what he was smelling and there was evidence of animals being up there through packing and droppings. Informed HO that he would need to get an exterminator or someone to come out but other than that his system looks clean.
Working on a Lennox heat pump
Complete duct and equipment changeout
Working on a York gas pack
Replacing a thermostat on a Carrier heat pump
Wiring repair and replaced thermostat on a Nordyne heat pump
Working on a Nordyne heat pump
Repairing a drain line on a Goodman heat pump
2 system Westinghouse heating maintenance
Replaced a contactor on a Goodman heat pump
Routine maintenance on Nordyne heat pump
Complete: 1 System EPA Maintenance Carrier Package Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Incomplete Trane Split HP 2 zone system: HO said unit was freezing up: At the HP found refrigerant around 25 and 30psi performed nitro leak search and found leak in condenser coil. The coil had dirt and mud caked on it from dogs digging. Had to rinse the coils off before performing leak search. Also leak search Evap coil and it seemed fine.
replacing a thermostat on a Payne heat pump