Took time and care by offering the various options available, the problems that needed to be addressed, and the work to be done.
Great personalities, very knowledgeable and extremely helpful
Extremely knowledgeable and professional gentlemen. Cody, Joel, and Marco got right to work and ensured the system was functioning at 100% before they left. They also gave extra care to our home and family. Finally, they ensured we were left in a position to fully utilize the new systems and all of its capabilities. Thanks, guys!
The service was second to none. Bought the system and it was installed within 24 hours and everyone from Comfort First was very professional. An outstanding company
Called to have someone diagnose and fix a small issue that I had with my system. Their techs knew exactly what it was and wasted no time getting me up and running. The expertise and professionalism provided by their experts is second to none.
Technician was very personable, knowledgable and patient to address all of our questions and concerns. He led us to make a well-informed decision in our purchase of needed equipment. GREAT JOB!
Technician was thorough and explained his diagnosis with possible solutions which may solve the problem.
Renee was very professional and friendly, she made the experience very easy and comfortable, since this was the first time I had to do this! The accuracy and timely manner things were taken care of just BLEW me away!!! I would definitely recommend this company and Renee to ANYBODY needing a heating/cooling system!
Working on a Trane heat pump
Working on a Trane heat pump
Replaced a thermostat on a Lennox heat pump
Working on a Payne heat pump
Working on a Nordyne heat pump
Replacing an evaporator coil on a Goodman air handler
Incomplete Trane Split HP 2 zone system. HO said wasn’t cooling started Friday and HP was short cycling. Had another company come yesterday and they are planning to do a leak search tomorrow. He wanted a second opinion. I found system short cycling. But it PRessures were 50 & 300. Checked upstairs and found no adjustable txv stuck closed. Added about 6oz of 410 with no change. Need new txv.
Goodman split Heat pump
Replaced a dual capacitor on a Westinghouse heat pump
Replaced a control board on a Carrier air handler
Complete: 1System: Carrier 2 zone Split HP: Came to replace txv. Removed refrigerant bc system couldn’t pump down. Removed 2 filter dryers from outside and brazed 1 new one back in. Then removed old txv. Blew system out with nitrogen and then installed new txv. Nitrogen pressure tested. Pulled Vacuum to 600 microns and it held. Charged with 9lbs of 410. System called for an 8 degree SC. And I was at 9. Delta T was 79 and 61. Spoke with HO for awhile had her laughing. All is good and system is working great at this time.
Replacing a blower motor on a Nordyne electric furnace
Leak searching a Goodman heat pump
Lennoxe aor handler checked system found blown 3 amp fuse and replaced and cycled system working at this time
Working on a Goodman heat pump