Carrier hp...bad cfm
Comfortmaker no cooling
Trane airhandler replaced fan relay
Appollo unit no ac
Complete two systems upper. Found bad 45/5 dual capacitor and replaced it. System is operating properly at this time.
Goodman condenser coils dirty
Complete: 1 system Amana Split HP: Switched out drain pan. Had to cut out Ptrap and piping remove wood panel in front of unit. Remove old pan, measure and cut wider hole in the floor. Cut and added pvc drain pan fitting to bottom of pan and running tubbing through the floor to the crawl space. Repipe condensate line back in, screw in male fitting tighter up into unit and screw wood panel back in from of system. With my water hose I added a lot of water to the primary drain with NO leaks. Place everything back together. Went into crawl space and cut both tubbing and pex pipe to lengthsI needed and ran tube into pex. Turned system on and is working great at this time. Left key back in lock box.
Just finished installing a new 2.5 ton Amana Ac/Coil and furnace also installed a new nest learning thermostat.
Comfortmaker.....replaced drain pan
Trane A/C completed cooling maintenance on down stairs system also found also found up stairs system to be low in refrigerant and quoted preferred leak search
Complete: Changed out evaporator coil for comfort maker split HP ...... added 9lbs of refrigerant
Comfortmaker replace coil
Comfortmaker ac...no cooling
Amanna heat pump adjusted sub cooling and cycled system working at this time