Devin and Josh were fantastic! They showed up on time, cleaned up after themselves and even caught a few things that had been overlooked before and tended to them as well. Thank you!
Devon and Joshua were professional and great technicians
Working on 2 Trane heat pumps
Cleaning a drain line on a Goodman air handler
Working on a Arcoaire heat pump
Replacing a control board on a Carrier air handler
Working on a Goodman heat pump
Water coming through vent Found drain line stopped up
Working on an Amana heat pump
Routine maintenance on Trane heat pump
Complete: 1 System 2 Zone Heil Split HP: HO said wasn’t coming on at all. At the AH in the crawl space found System shut off by the condensate pump. Found tubing clogged and tripped breaker to condensate. Blew out tube, cleaned Ptrap and system came on perfect. Checked charge and system is working great at this time.
Complete: 1 system Goodman split hp: HO said had no signal on Tstat. At AH found blown fuse. Traced short back to reversing valve solenoid. Was going to get a solenoid from East Coast but called Jimmy and he had one in Warehouse Stock. He delivered it. The HO had to leave so we put new solenoid on and tested the unit from the outside.
Installing a UV light on a Goodman air handler
Incomplete 1 System Worked on a Goodman Heat Pump Split System HO said Unit was not keeping desired temperature . Evap. Coil and outside sunction lune was freezing up. Found Unit way too low in refrigerant. Unit holds 14 lbs. and 8 oz of R22 so we started a leak search but when we started rain started pouring a lot of rain. Left nitrogen at 290 psig. Need to reschedule to continue leak search. Spoke with HO completely understands and he thinks they might have been low in refrigerant for some time
Working on a Rheem heat pump
Routine maintenance on Payne heat pump
Goodman split heat pump no cool