BJ was very knowledgeable about the products/installation. Great attitude, great service, very patient & took his time to do things correctly.
Excellent Service. Very efficient and took time to answer all our questions
Great service, prompt, friendly, knowledgeable, and efficient— a real value and great customer experience. Cody is a great technician!
The technician was prompt, thorough, and took time to explain the problem. Great service!
Cody was great. Efficient , very thorough and friendly. Always a pleasure working with Comfort First.
Complete: 2 Systems: Worked on downstairs Unit and 2nd and 3rd Floor 2 zone unit. Came to install 3 nest thermostats, Nest Doorbell, Google HomeHub and Google mini. Installed the US 2 zone system tstats ran tests and working great at this time. Installed DS Tstat ran tests and system is working great at this time. Installed doorbell. Ran test. Doorbell works great. He is having WiFi issues to the doorbell camera being the routers are on the third floor and door bell down on the bottom floor front door. Recommended researching WiFi extender. Other than the delay on the doorbell camera showing up on his phone the doorbell is working great at this time. Installed two google products and walked customer through setup for nest and google products on his phone. All devices installed and working as they should at this time, apart from WiFi issues to the doorbell.
Carrier a.c.. Replaced faulty condenser fan motor with new and ensured proper operation
Rheem A/C EPA maintenance
Trane A/C EPA maintenance
Trane gas pack replaced collector box added 1lbs R22 refrigerant
Trane split system found evaporator coil leaking
Repairing a Goodman Package Unit
Lennox replaced blower motor and capacitor
Trane 3rd floor bad cfm and blade
Trane 2nd floor found no issues
Trane AC downstairs found no issues
Complete to system maintenance Lennox split heat pump‘s upstairs and downstairs checked the charge amp drawls capacitors it washed units. Systems look good
Incomplete: 3 Systems: Worked on Rt Side Of House System. TRANE Split Heat Pump. Came to replace compressor, cap and dryer. Recovered refrigerant, Unbolted Compressor, bolted new one in. Changed cap and dryer. Pressurized with Nitrogen and pulled vacuum system held with both. Put in 4.5 lbs of refrigerant and my superheat was off with a low side pressure of 40. Added another lb of refrigerant with minimal change. Found inside filter completely stopped up and washed condenser Coils.
2 system EPA and sold maintenance agreement
Goodman inspected duct work