Complete 1 System Lennox HP Split System: HO stated they would set tstat at 68 but system would never cut off when reaching set temp. Cycled system and made sure sequencer and fan relay were working properly. Found bad tstat. It wouldnt cut system off when moving tepm lever down. Replaced it. Used a Proselect non prog tstat from truck stock. Cycled system. System is running properly at this time.
Wall heater not staying lite
Goodman equipment.....low on charge
Goodman eq...no cooling
Incomplete: 2 systems worked on DS Unit: Trane Gas Package unit. Came to install ecobee Tstat and add 1lb of 410a. Installed Tstat and setup on customers to phone and cycled system. In the heat mode was going to add refrigerant due to outdoor temp. System tripped out on low pressure but extremely high pressure. Found filter, condenser coil and evaporator coil stopped up. Cleaned coils and replaced filter. System still dropped on low. Switched to cool mode and system ran great with pressures looking great. Need to order new Condenser TXV.
Rheem heat pump checked system found low voltage short and repaired and cycled system working at this time
Rheem no ac
Goodman A/C checked system found to be low in refrigerant and added 2 lb R-22
Carrier heat pump checked system found to be low in refrigerant and added 1 lb R-22 and cycled system working at this time
2 rheem 15.5 seer heat pump split changeout