Carl was great from start to finish. Handled everything professionally and quickly. Replaced a new fan motor in about 30 minutes after quickly diagnosing the issue. Thank you!!!
Serviced trane heat pump -had to add refrigerant -
Worked on Trane heat pump preformed Leak search found leak at condenser coil ordering part to repair
C Goodman heat pump found to be low in refrigerant and preformed leaks search and found leaking accumulator
Goodman heat pump found low voltage short and repaired
Rheem heat pump replaced leaking evaporator coil and recharged system with 5 lb R-22
Found system low in refrigerant
Checked system found bad condenser fan motor and replaced and cycled system working at this time
AC repair and maintenance service.