Grateful to Justin for make my oceanfront cool again! Lightning fast repair service. Fast scheduling! Parts available onsite in truck!
Justin Manners was great. Got here when he said he was going to get here and took great care of our HVAC system.
Justin did a great job explaining everything. He was very thorough. Cost was much more than I anticipated due to two extras costs on top of the system check cost.
Justin did great! Very friendly and thorough, I feel good about my service plan through Comfort First!
Carl was great from start to finish. Handled everything professionally and quickly. Replaced a new fan motor in about 30 minutes after quickly diagnosing the issue. Thank you!!!
EPA Maintenance Visit.
Complete two systems, down. Found bad thermostat and replaced it. System is operating properly at this time.
Complete two systems. Found primary drain lien clogged and cleared out. System is operating properly at this time.
Serviced trane heat pump -had to add refrigerant -
Worked on Trane heat pump preformed Leak search found leak at condenser coil ordering part to repair
C Goodman heat pump found to be low in refrigerant and preformed leaks search and found leaking accumulator
Goodman heat pump found low voltage short and repaired
Rheem heat pump replaced leaking evaporator coil and recharged system with 5 lb R-22
Found system low in refrigerant