Installers were pleasant and did a great job!
Just finished up installing a new 2.0 ton Amana Split Heat Pump. Upsized a return from 14 inch flex to 16 in flex.
Provided an estimate for the customers to replace their split heat pump. We will be installing the system this week.
Complete: 2 Systems: Worked on Upstairs Unit: Goodman Split HP: HO said feels like hot air blowing when in cool mode. At HP found reversing valve not energized. Power was coming into and out of board. Then checked solenoid and found one of the wires had come loose. Placed wire back on and reversing valve energized. Cycled system on and off and system is working great at this time. $0 Collected
Working on goodman gaspack
Heating maintenance on a Goodman package heat pump
Heating maintenance on a Amana gas pack
Heating maintenance on 2 Amana heat pumps
Working on goodman package heat pump.
Found a bad cap and nonprogrammable thermostat on a Gas Pack
Working on a Split system Goodman Hp that had a bad capacitor on blower motor
Just finished installing a 3.5 ton Amana package heat pump.
Meeting with a customer to discuss replacing his packaged heat pump.
Meeting with an existing customer to discuss replacing the duct work now. We already replaced the heat pump package unit, and now they would like the ducts replaced as well.
Helped a customer find the best system to fit her needs for her rental home. We are replacing her Goodman with a 14 seer Amana and a few duct modifications to correct air flow. The system was also oversized according to the load calculation, so we corrected that issue as well. Customer is very happy. We were able to get her approved with 100% financing and we are installing in just a few days.