Installers were pleasant and did a great job!
Complete: 1System Rheem Gas Package Unit: HO said TN cut breaker off and when he cut it back on it stopped working. Found condenser motor bad. It had a rescue motor on it but didn’t have a rescue to match. Had to call dealers for OEM details. I used a 1/5hp 1075 protech motor. Had to rewire and run new and add a 5 cap. Cycled system and working great at this time.