Installers were pleasant and did a great job!
Replaced evap coil on rheem split heat pump
Install 12kw Briggs & Stratton Fortress whole home generator
Lennox split heat pump no heat
Installing whole home generator
Installing new generator
Installed a new Briggs and Stratton 12 kw whole home generator
Found and defrost relay on Rudd split heat pump
Completed epa on Goodman straight ac
Found empty propane tank on Goodman gas pack
EPA maintenance cooling on 2 system amana heatpump split system
Just finished installing a new 2.5 ton Amana Gas Package unit and 12 supply 1 return duct system. Also installed new Nest Learning Thermostat.
Installed new gree mini split heating and cooling system
Groover Complete: 1 systems: Trane Split HP: During EPA Maintenance found system low in charge. Informed HO and added 2lbs of r-22 and 1 can of leak stop. Cycled system and system working as it should at this time. Collected $267.50 for 2lbs of r22 via cc sq
Complete: 1 System: EPA Maintenance Goodman Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Repaired duct on Goodman gas pack