Installers were pleasant and did a great job!
performed heating maintenance on Goodman heat pump AC split system upper and lower.
Found bad inducer motor on nuton gas pack
Working on a goodman gaspack
Found Goodman split heat pump out of Freon
Replaced heat exchanger on Goodman gas pack
Replaced compressor on Trane split heat pump
Replaced compressor variable speed CFM and CFM control board on Trane split heat pump
Replaced evaporator coil on Goodman split heat pump
Gas pack found blower motor spinning backwards causing lack of air flow
Just finished up installing a new 2.0 ton Amana Split Heat Pump. Upsized a return from 14 inch flex to 16 in flex.
Provided an estimate for the customers to replace their split heat pump. We will be installing the system this week.
Complete: 2 Systems: Worked on Upstairs Unit: Goodman Split HP: HO said feels like hot air blowing when in cool mode. At HP found reversing valve not energized. Power was coming into and out of board. Then checked solenoid and found one of the wires had come loose. Placed wire back on and reversing valve energized. Cycled system on and off and system is working great at this time. $0 Collected
Working on goodman gaspack
Heating maintenance on a Goodman package heat pump
Heating maintenance on a Amana gas pack