Complete two systems. Found water in secondary drain pan due to clogged primary drain line. Cleared out the drain line. System is operating properly at this time.
Complete two upstairs heat pump. Found the emergency drain pan full of water. Cleared out drain lines and drain pan. Tested drain and assured that it was working properly. System is operating properly at this time.
Replaced compressor on trane heat pump,found other issues ,ordered part-defrost board
Repair burnt wire in air handler Cycle System running properly
Trane gas pack replace contral board and cycled system
Confirmed proper operation on York gas pack