Over the last year I have dealt with Comfort First several times. First time was during a home insurance appointment and I was so impressed that I did a maintenance program with them. Each person coming out to my home has been so nice and explained everything simply for me So glad that they were the one who were assigned. I will be continuing using their services for hopefully a very long time!
Trane hp....no ac
Amanna gas packs completed EPA cooling maintenance and cycled system working at this time
Just finished installing a new 3.0 ton Amana Heat pump and electric furance. Also installed a new Nest Learning Thermostat.
Incomplete: 2 System: worked on right side of home. Trane Gas Package unit came to perform EPA and found back up heat GaS LP not coming on: Found burnt flame sensor wire repaired it also found very rusted burners. Cleaned them and flame sensor. A lot of rust was coming out of heat exchanger. I turned unit on and the flame was rolling out severely. Found cracked Heat Exchanger. Need to replace heat exchanger and two burners:
Goodman heat pumps completed heating maintenance and cycled system working at this time
Coleman AC common wire broke loose on the outside fan motor
Comfortmaker hp board
Miller heat pump intermittent control board outdoor unit
2 trane A/C systems completed EPA cooling maintenance
Goodman gas furnace checked system found open pressure switch due tostopped up vacuum line and cleared and cycled system
Goodman gas pack not heating
Goodman gaspack..no heat
Trane equipment furnaces tune up