Over the last year I have dealt with Comfort First several times. First time was during a home insurance appointment and I was so impressed that I did a maintenance program with them. Each person coming out to my home has been so nice and explained everything simply for me So glad that they were the one who were assigned. I will be continuing using their services for hopefully a very long time!
Amana gas furnace performed cooling maintenance
Lennoxe heat pump checked system found to be lpw in refrigerate amd repaired leaking service valve and added 1 lb R438A and cycled system working at this time
Lennox heat pump replaced compressor bi flow drier capacitor and recharged system with refrigerate and cycled system working at this time
Incomplete 1 System American Aire HP Split System. HO stated system was just blowing warm air. Found blown 30Amp fuses, small kind. Before using new ones I checked compressor. Found compressor grounded. Will need compressor replaced. Will need original one. Arco compressor wont fit. System hold 7 lbs of R22. It will need 2 small 30Amp fuses. Need a PO# to order compressor. Talked to HO about the situation.
Complete 2 System worked on both LeftSide Goodman GasPak/Straight A/C Straight A/C and RightSide Amana Dual Fuel Gas Pak/ Came to perform EPA Cooling Maintenance on both systems. LeftSide Goodman GasPak Straight A/C: Checked thermostat and air filters. Replaced air filter. Checked blower motor amp draws. Checked run cap. Checked all wiring. Inspected evap coil and blower wheel. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Cleaned condenser coil. Checked pressures. System is running great at this time. RightSide Amana Dual Fuel HP Pak Unit. Checked thermostat and air filters. Replaced air filter. Checked blower motor amp draws. Checked all wiring. Inspected evap coil and blower wheel. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Cleaned condenser coil. Checked pressures. System is running great at this time.
Complete 1 System Carrier Straight A/C. HO Stated system was blowing regular air and that system outside was not running. Found Bad dual cap. I needed a 55+7.5, I didnt have in stock, I had to use a 45/7.5uf and 10uf caps to make a 55/7.5. From truck stock. Checked pressures. System is running great at this time.
Installed Briggs and Stratton 20KW whole home generator
Replaced control board Westinghouse package
Trane....equipment check heating cycle
Lennox gaspack heating maintenance
Install 20 kw Briggs & Stratton fortress whole home generator
Coleman package unit bad compressor
Amanna heat pump checked system found to be low in refrigerant need to preform leak search on system to locate leak
Trane hp....no ac