Incomplete 1 System American Aire HP Split System. HO stated system was just blowing warm air. Found blown 30Amp fuses, small kind. Before using new ones I checked compressor. Found compressor grounded. Will need compressor replaced. Will need original one. Arco compressor wont fit. System hold 7 lbs of R22. It will need 2 small 30Amp fuses. Need a PO# to order compressor. Talked to HO about the situation.