Repair a Goodman Heat Pump
Replaced a evaporator coil on a nordyne heat pump
Replaced evaporator coil on a Payne heat pump
We installed a. 2 ton lennox heat pump package unit with 5 kw heat kit and replaced 9 6"supply runs
We installed a 3 heat pump with a amana air handler with ten kw heat kit
Nordyne heat pump checked system found to be low in refrigerant and added 2 lb R-410
Amanna heat pump completed EPA cooling maintenance
Carrier heat pump reclaimed refrigerant replaced compressor bi flow drier capacitor and pulled vacuum and recharged system with 7 ph R-438A
Fixed gas furnace. Cleaned burners
Replaced start capacitor on ptac ac unit
Oiled condenser fan motor to prevent possible screeching noise on trane heat pump
Replaced draft motor on Rheem high efficiency furnace
Found thermostat not operating properly. Replaced thermostat and checked operation of Goodman heat pump. System working as it should at this time.
Found tripped breaker. Reset breaker and install hard start to help with start amp. System working as it should at this time.
Replaced capacitor on a split 1.5 ton carrier heat pump