Billy did a great job and answered all my questions. He went above and beyond by ensuring my condensate line was clear...which is was not and was actually buried. Awesome service from Billy...he represented the company perfectly.
Both Anna and Billy were very helpful. Thank you both for your prompt and courteous service!
Billy was awesome. I really appreciate the way he explained everything to me and even took the time to show me pictures. I definitely trust his judgement and that means a lot because a lot of companies take advantage. I have always had great experience with this company as a whole
Working on York heat pump
Worked on ductwork
Worked on Goodman air conditioner
Worked on Trane air conditioner
Airese...gas pack maintenance
Trane gas furnace checked system found dirty flame sencer and cleaned and cycled system working at this time
Trane heat pump bad contactor
York heat pump completed EPA heating maintenance and cycled system working at this time
Trane package unit...
Goodman gas pack replace control board
Trane gas pack repair
Comfortmaker furnace check
Goodman gas pack repair
Goodman gas pack checked system found draft inducer motor not running due to bad contral board
Trane heat pump checked system found compressor not starting due to bad capacitor and replaced and added hard start due to compressor pulling high start amps and cycled system working at this time