Explained my new system to me that I could understand before leaving Took their time and didn't rush made sure everything was cleaned up
Technician was very knowledgeable and courteous. Seemed very thorough!
Billy did a great job and answered all my questions. He went above and beyond by ensuring my condensate line was clear...which is was not and was actually buried. Awesome service from Billy...he represented the company perfectly.
Both Anna and Billy were very helpful. Thank you both for your prompt and courteous service!
Billy was awesome. I really appreciate the way he explained everything to me and even took the time to show me pictures. I definitely trust his judgement and that means a lot because a lot of companies take advantage. I have always had great experience with this company as a whole
Complete 2 Systems worked on Us Goodman HP Straight A/C: HO stated system outside was not cooling. Found bad contactor. Used a 1 1/2 Plle contactor from trock stock. Found system 2 lbs low in ref. Added 2 lbs of 410A and a leak seal. System is running great at this time.
Complete 2 Systems worked on US Goodman Straight A/C: HO stated system was not cooling. Found bad dual cap at the condenser. Used a 35/5 cap from truck stock. Checked pressures. System is running great at this time.
Goodman ac.....replaced evap/coil
Goodman hp not cooling
Goodman hp no cooling
Fan running constantly
Goodman no heat
Goodman replaced compressor and cycled systems working at this time
3.5 tons amana heat pump pack
Ac and coil 2.tons
Trane A/C checked system found to dual run capacitor and replaced and cycled system working at this time
Airease replaced heat exchanger and cycled system working at this time
Goodman no cooling
Goodman ac low charge
Airese crack heatexchanger