Incomplete 2 Systems worked on a Lennox A/C. HO stated system was not working properly. Tuened system on. Outdoor unit didnt come on. Manual reset switch on discharge line was tripped. Reset but it only ran for a few secs. Bypassed it, to checked pressures. Pressures were looking great. Manual Hi Pressure switch needs to be replaced. Called Jimmy, to ask if ref needs to be removed, he said yes it does. System holds 7 lbs of R410A. Condenser Data: M#: 14CX-018-230-12. S#: 1911M14831. P#: 100103-03. Price: $28.71+ tax. 1 available at Raleigh store. Did not order due to HO saying before he agrees the nons he is going to call AHS. Will need a PO# if HO agrees to nons.
Heat Pump Heat maintenance
Gas Heating Maintenance