Worked with several technicians during the project to replace the downstairs A/C unit as well as office staff on the phone. Very happy with my results. Great team to work with.
Quoted and installed an Aprilaire whole-house humidifier. Eight days from requesting quote to installation complete. At price quoted. Which was discounted from retail hardware pricing shown on Amazon and other sites. Service personnel were thorough and very helpful in explaining the system. We're going to go with an annual service plan based on this very satisfactory initial experience.
Response from Comfort First Heating and Cooling:
Gordon, we are so glad your whole-house humidifier installation was a success! Thank you so much for an amazing review. We look forward to fulfilling your service plan!
They were very upfront about pricing. The guys that came to install the units were great and did a great job to make sure it was done right.
He was very knowledgeable and honest. Very personable also.
Bill was very pleasant and courteous. Explained everything in great detail.
They install team did a great job, but I’m confused as to why my water heater is not working now.
Great job. Thank you Bill !
Complete 1 System Goodman HP Split System. HO stated system was blowing hot air. Found bad dual cap. Used a 55/5 dual cap from truck stock. Pressures are great.
Complete 3 Systems worked on Us Carrier A/C System. Austin and I replaced case coil. Removed old coil. Insfalled new coil. Made mods to drain line and ref lines. Leak tested system. Pulled vacuum. Added 8 lbsof 410A. System is running great at this time.
Carrier equipment heating maintenance
Rheem hp....not heating
Carrier split heatpump preformed heating tuneup
Installed humidifier and uv light
Goodman gaspack not heating
Carrier split heat pump performed heating maintenance
Complete 1 System 2 Zones Carrier 90% Gas Furnace: replaced inducer motor. Tested. Cycled system. System isnrunning great at this time.
Goodman split heat found low on refrigerant
Installed ac coil and condenser
Goodman heat pump checked system found bad dual run capacitor and replaced and cycled system working at this time