I experienced excellent service. This tech went beyond his call of duty. I would strongly recommend this company to a friend or relative.
Very thorough, honest, and personable
Appreciate the tech sent. Thomas was savvy and professional. He made sure all was in good working order before leaving Great experience
Very knowledgeable, friendly, helpful, went above and beyond and helped me with another issue with another company (propane company)
Complete 1 System Goodman HP Split System HO said system was not coming on. Turned thermostat on blower motor didn’t come on. Found a bad 5 ufd capacitor and replaced it. Drain pan was full of water. Drain line was stopped up. Cleared drain line. Checked motor amps. Checked pressures. System is running great at this time.
Complete two systems up split heat pump. Found bad 30+5 capacitor and replaced it. Found unit low on refrigerant and added 1 lbs of R22. System is operating properly at this time.
Complete one system. Found dirty air filter and removed it. Found dirty condenser coil and cleaned it. System operating properly at this time.
Complete: 2 systems worked on Both Units: Carrier split HPs: HO said both units weren’t cooling to desired temp. Delta T was 10° DS and 5° US. On the US and DS systems both were low in refrigerant. Added 2lbs of 410 , leak seal and hard start to both. Checked Temps again and the DS was 17° and US was 20°. Systems working great at this time.
Bad blower capacitor on goodman heatpump package unit
Loose wire on trane split system straight ac
Bad capacitor on Goodman heatpump for upstairs
Puron split heat pump found system to pounds low on 410 a
Train split heat pump found P-trap clogged and found system to pounds low on r22
Goodman gas furnace. Diagnosed bad blower wheel
Trane split straight a.c.. Replaced evap coil and txv
Goodman split heat pump found compressor bad
Carrier split heat pump found restriction in line set Causing system not to cool properly
Lennox gas furnace performed cooling maintenance