Comfort First is a great Company to take great care in heat and air servicing your units. This company is prompt and very knowledgeable in the area. They are affordable and will offer financing to struggling families. Customer service is of the finest quality.
I experienced excellent service. This tech went beyond his call of duty. I would strongly recommend this company to a friend or relative.
Very thorough, honest, and personable
Appreciate the tech sent. Thomas was savvy and professional. He made sure all was in good working order before leaving Great experience
Complete 1 System Goodman A/C: replaced compressor, condenser motor, and dual run cap. Removed 2 old filter dryers repiped inside condenser unit. Installed new filter dryer outside unit. Installed new compressor. Leak tested system. Pulled vacuum. Added 10 lbs of 438A. Replaced condenser fan motor. Replaced dual run cap. 55/5 Uf from truck stock. Checked pressures. System is running great at this time.
Goodman ac check
Performed cooling maintenance on Trane split heat pump
Amana ac check
Complete 1 System 2 Zones Ametican Standard HP Split System. Came to replace compressor. Recovered refrigerant. Removed old compressor and filter dryer. Installed new compressor and filter dryer. Leak tested. Pulled vacuum. Added 8 lbs of 410A. Tested system. Contactor was not working properly. Bad contactor. Was making a very loud noise. Replaced contactor with a single pole contactor from truck stock. HO was interested on giveing maintenance to system. Sold him an EPA. HO wants to get pay the epa monthlt. Checked pressures. System is running great at this time.
Goodman split heatpump preformed cooling maintenance
Lennox split heatpump cooling maintenance
Goodman gas pack checked system found bad gas valve
Goodman split heat pump. Added refrigerant
Amanna heat pump checked system found to be working and maintaining temp at this time
Goodman split straight a.c. checked system for proper operation
Amana split heat 9ump. Installed nest thermostat
Carrier split straight a.c. with gas furnace. Diagnosed leaking service valve
Trane split straight a.c.. Added refrigerant