Comfort First is a great Company to take great care in heat and air servicing your units. This company is prompt and very knowledgeable in the area. They are affordable and will offer financing to struggling families. Customer service is of the finest quality.
I experienced excellent service. This tech went beyond his call of duty. I would strongly recommend this company to a friend or relative.
Very thorough, honest, and personable
Appreciate the tech sent. Thomas was savvy and professional. He made sure all was in good working order before leaving Great experience
Goodman split heat pump replace compressor
Train split heat pump found unit 2 pounds low on our 22
Goodman split heatpump replaced compressor capacitor and filter drier charged system with 9lbs of 438a
Carrier split heatpump found bad zone motor
Carrier split heat pump replaced TXV
Carrier package heat pump replaced TXV
Lennox repair refrigerant leak
Complete 1 System Rheem HP Split System. EPA Cooling Maintenance. Checked thermostat and air filter. Checked run cap. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Complete 1 System York HP Split System. HO stated that he just wanted to make sure system was running properly. Checked tstat and air filter. Cycled system. Checked pressures. Checked amparage on compressor and cfm. SYSTEM is running great at this time.
Train split heat pump diagnosed bad discharge air temperature sensor
Complete 1 System Goodman A/C: replaced compressor, condenser motor, and dual run cap. Removed 2 old filter dryers repiped inside condenser unit. Installed new filter dryer outside unit. Installed new compressor. Leak tested system. Pulled vacuum. Added 10 lbs of 438A. Replaced condenser fan motor. Replaced dual run cap. 55/5 Uf from truck stock. Checked pressures. System is running great at this time.
Goodman ac check
Performed cooling maintenance on Trane split heat pump
Amana ac check