I experienced excellent service. This tech went beyond his call of duty. I would strongly recommend this company to a friend or relative.
Very thorough, honest, and personable
Appreciate the tech sent. Thomas was savvy and professional. He made sure all was in good working order before leaving Great experience
Very knowledgeable, friendly, helpful, went above and beyond and helped me with another issue with another company (propane company)
Fixed a 3 yr recurring issue in an hour.
Puron split heat pump found system to pounds low on 410 a
Train split heat pump found P-trap clogged and found system to pounds low on r22
Goodman gas furnace. Diagnosed bad blower wheel
Trane split straight a.c.. Replaced evap coil and txv
Goodman split heat pump found compressor bad
Carrier split heat pump found restriction in line set Causing system not to cool properly
Lennox gas furnace performed cooling maintenance
Complete 2 System worked on US Carrier HP split System. HO said system was freezing up and not cooling and some times it wouldnt come on. Checked Air Handler wiring and found the yellow wire broken almost falling out of wire nut. Fixed it. Checked refrigerant and also found low. Added 2 lbs of R22 and 1 can of leak stop. System running great at this time.
Puron split heatpump replaced condenser fan blade
Complete 2 system worked on DS Carrier HP split system HO said system was not cooling and that blower sometimes wouldnt blow any air or just a little. Found blower motor run capacitor bad. Replaced Run Capacitor (5 UFD). Also found refrigerant charge low. Added 1 lbs of R22. System Looks Good and Running Great At This Time.
Complete 1 System worked a Goodman Straight A/C Unit HO said he was hearing a really loud noise coming from the AH in the attic. Found a Bad blower motor, and also one of the legs on the motor mount bracket was broken. Replaced old motor with a 1/2 hp 120v motor (P#: 1865) and installed new 5-5 1/2 mount bracket (P#: TFM556) Tested motor. Checked Refrigerant Charge. System Looks good and running great at this time.
Bad compressor carrier split system heatpump
Carrier split heatpump replaced accumulator and evaporator coil
Carrier split heatpump replaced compressor and charged with 6lbs 438a refrigerant
Amana split heatpump found outdoor txv bad