Complete 1 System Rheem HP Split System. EPA Cooling Maintenance. Checked thermostat and air filter. Checked run cap. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.