Worked on Trane air conditioner
No one home need to reschedule when some one can be available
Airease...hp bad compressor
Trane gas pack checked system found to be working and maintaining temperature at this time
Lennox ac completed cooling maintenance and cycled system working at this time
Tempstar heat pump package Unit no heat
Heating tune up...
York Furnace no heat
Goodman furnace....flame senor dirty
Incomplete: LG Mini split: Wasn’t blowing hot air. At the Outdoor unit found compressor terminals unattached from top of compressor. Needs new compressor. Need to order in the AM. Talked to HOs mother and she is ok with Beth giving her a call about options towards a new system. Pics in Docs
Carrier gas furnace checked system found bad blower motor and replaced and cycled system working at this time
Goodman gas furnace completed heating maintenance and cycled system working at this time
Armstrong package unit....
Goodman heatpump blown capacitor 1bl low r22
Ruud A/C completed cooling maintenance