Very good service let me know what was wrong was very straightforward and kind. Brought my dogs some treats which they are very happy. We all are.
Billy saw what the problem was in 5 minutes or less and even talked to me as he worked to explain what happened.
Very helpful with recommendations
Complete 1 System Goodman Pak System System: EPA Cooling Maintenance. Checked tstat and air filter. Checked blower motor amp draw. Inspected all wiring at the AH. Inspected evap coil. Drain line found clear. Checked compressor and cfm amp draws. Checked pressures. Inspected all wiring at the condenser unit. Checked dual cap. Cleaned condenser coil. System is running great at this time.
Incomplete 1 System (year2009) Trane Dual Fuel Gas Pak: HO stated system was tripping breaker. Found compressor grounded.
Replace idm carrier gaspack
Complete 2 Systems Worked on DS Amana Straight A/C: EPA Cooling Maintennace: Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Rheem gas pack checked system found zone system unwired and not in operation casing temp to be higher on second floor need to added thermostat and rewire zone system
Trane heat pump replaced Indoor TXV and pulled vacuum and added 1 lb R-410 refrigerate and cycled system working at this time
Trane heat pump amd air handler checked system found bad indoor TXV need to replace indoor TXV
Payne gaspack...evap/coil leaking
Carrier gaspack low refrigerant
Carrier gaspack low charge r22
Lennox ac check
Work on Amana gas furnace
Worked on Goodman heat pump
Worked on Carrier gas furnace
Working on Amana gas furnace