Trane Gas Pack thermostat
Amana and heatpump inspection
Installed new split system
Complete two systems, upstairs. Found bad condensate pump and replaced it. Systems are operating properly at this time.
Install 13 kw Briggs and Stratton generator
Replaced nest tsat
Installed 3 ton Amana heat pump.
Bryant split ac with gas heat. Diagnosed blown 50 amp fuse in service disconnect and a bad dual capacitor. Replaced fuses and dual capacitor. Ensured proper operation
Provided an estimate for a customer to replace both of their split heat pumps.