Complete two systems, upstairs. Found bad condensate pump and replaced it. Systems are operating properly at this time.
Install 13 kw Briggs and Stratton generator
Replaced nest tsat
Installed 3 ton Amana heat pump.
Bryant split ac with gas heat. Diagnosed blown 50 amp fuse in service disconnect and a bad dual capacitor. Replaced fuses and dual capacitor. Ensured proper operation
Provided an estimate for a customer to replace both of their split heat pumps.