From the beginning to the end and everything in between, they take “special” care. What impressed me most was that they could answer any question, even if I thought it was a silly question.
Awesome job installing new unit. On time, polite and courteous. They were in did their job in timely manner and cleaned up everything when job was completed. Highly recommend.
Wonderful service great technicians
Billy was polite, helpful, and answered all questions. Very professional. Thank you for sending him!
The technician was great
Bill did a wonderful job providing me with all my options.
Very helpful. Willing to take the time to explain things.
Billy arrived early and provided exceptional service! He gave supreme knowledge of our AC’s condition and concern that we were w/o ac for so long. He went right to work. He was compassionate, kind, efficient and most importantly safe! :) Not to mention very professional. It took him no time to get it AC repaired and he provided service with a kind smile! He makes the company look good! Thank you Billy for your standard of excellence!
Complete 1 System Goodman HP Split System. Replaced fan control board, transformer, and tstat. Took me more time due to wiring at control board was out of place. Had to follow schematic tonconect all wires in the right place. Had to add a 5 amp fuse for transformer and board. Tested. Tstat was not sending signal for blower motor to come on. Replaced tstat. Used a non prog proselect tstat from truck stock. Tested again. System came on. Checked pressures. System is running great at this time.
Complete 1 System Goodman Straight A/C EPA Cooling Maintenance. Checked thermostat and air filters. Checked blower motor amp draws. Checked run cap. Checked all wiring. Inspected evap coil and blower wheel. Checked run cap. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Cleaned condenser coil. Checked pressures. System is running great at this time.
Icp gas pack
American Standard A/C checked system found tripped breaker in main panel box due to bing bad need to replace
Rheem Package heat pump checked system found compressor not runing due to being bad need to replace compressor
Trane gas pack completed ASH cooling maintenance and cycled system working at this time
Comfortmaker gas pack checked system found compressor and CFM not running due to bad contactor and replaced and cycled system working at this time
American standard replaced Hardstart
Replaced suction valve
Trane airhandler evap/coil leakin
Goodman Heat Pump
Installed ac and gas furnace
Trane heat pump checked system found lose witing connections at service disconnect and repaired and cycled system working at this time
Rheem A/C completed cooling maintenance and cycled system working at this time