First class from beginning to install!
Very nice, showed me what he did, quick.
Billy did a fantastic job - took time to explain everything to me. Really appreciate the great service!!
My technician Bill was very friendly and knowledgeable. He took the time to explain the workings of my furnace, what he was looking for and how to fix it.
Billy was great, explained everything to me in terms I could understand. He was polite & very professional. I was very impressed!
Everyone was professional and knowledgeable.
Arrived on time. Timely work. Good cleanup.
Billy and Eric were professional and personable. They fixed the thermostat issue and made sure everything was working correctly. They explained how to work the thermostat and asked if I had any questions. Thank you! Billy and Eric for excellent work and customer service.
Billy and Eric did a great job at identifying the issue with our hvac system and came very early in the time window given (huge convenience). Overall a great experience.
Tempstar completed EPA heating maintenance and cycled system working at this time
Rheem A/C and case coil with gas furnace checked system found systwm not drining due to no vent in primmy drain line and repired
Rheem furnace heating maintenance
Complete 1 System Lennox Gas Pak EPA Heating Maintenance: cycled system. Checked tstat and air filter. Checked electrical connections. Inspected evap coil. No CO2. Burners are clean. Cleaned All safety switches are on great condition. Checked draft motor amp draws and cap. System is running great at this time.
Amanna gas pack completed EPA heating maintenance and cycled system working at this time
Whirlpool A/C checked system found run wire not connected causing compressor not to run and reconnected and cycled system working at this time
Complete 1 System ThermoPride Straight A/C: Checked thermostat and air filters. Checked blower motor amp draw. Checked run cap. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Complete 1 System Goodman Gas Furnace: EPA Heating Maintenance: cycled system. Hecked air filter. Checked blower motor amp draws. Checked run Cap. Checked electrical wiring. Cleaned flame rod. Inspected heat exchanger. Tighten up screws. Inspected burners. System is running great at this time.
Goodman furnace repired wire for condensation pump and installed co deoctor in master bedroom
Goodman heat pump checked system found to be low in refrigerate and added 2 lb R-410 to system and cycled system working at this time
Carrier replaced wiring harness and transformer and cycled system working at this time
Comfortmaker heat pump checked system found blown 30 amps fuses at service disconnect due to grounded compressor need ro replace compressor
Carrier checked system found stopped up primmy drain line and cleared and cycled system working at this time
Carrier air handle replaced blower mootr and found high voltage short need ro replace heat strips