Bradley McLeod delivered wonderful customer service. He was professional and courteous and took care of what we needed very quickly!
Answered all my questions and was very timely. Great customer service
Tony came and got us ready for winter! Thankful for his knowledge and service.
Professional, great personality and very good job!
Andy did a great job to narrow down what was causing my unit not to work. Grant it’s 100 degrees and I know they just want to get home. He was very thoughtful and willingness to find out why it stopped working in the first place was a great welcome. The unit started working before even looking at it and both of us were in awe of why. But Andy didn’t just want to leave without going thru every possible reason of why it happened in the first place. Most people would have said “I don’t know what to tell you?” But he insisted we figure it out. Eventually we found the culprit and was quick to get it up and going. Thanks for your help. Andy did an excellent job!
Glad i only had to wait two days for service.
Billy did a great job, and was very professional and personable. I was highly impressed with the speed in which he replaced the capacitor.
Carrier gas pack repair
Carrier gas pack checked system found system short cycling due to bad flame sencer and control board need to replace both
Comfortmaker furnace repair
Trane furnace check
Comfortmaker furnace check
Comfortmaker gas pack repair
Tempstar gas pack replaced draft inducer assembly and cycled system working at this time
Arcoair gas pack checked system found open pressure switch due to bad draft induce motor need to replace draft induce assembly
Goodman gas furnace completed EPA heating maintenance and cycled system working at this time
Snyder General gas furnace checked system found blown low voltage transformer and replaced and added 5 amp fuse and cycled system working at this time
Goodman ac replaced primary drain pan and cycled system working at this time
Comfortmaker Heat Furnace
Comfortmaker gas pack replaced heat exchanger and faceplate and cycled system working at this time
Goodman Split system Heat Pump
Goodman heat pump checked system found blown 5 amps fuse due to thermostat being wired wrong and corrected and replaced fuse and cycled system working at this time