Very nice, showed me what he did, quick.
Billy did a fantastic job - took time to explain everything to me. Really appreciate the great service!!
My technician Bill was very friendly and knowledgeable. He took the time to explain the workings of my furnace, what he was looking for and how to fix it.
Billy was great, explained everything to me in terms I could understand. He was polite & very professional. I was very impressed!
Everyone was professional and knowledgeable.
Arrived on time. Timely work. Good cleanup.
Billy and Eric were professional and personable. They fixed the thermostat issue and made sure everything was working correctly. They explained how to work the thermostat and asked if I had any questions. Thank you! Billy and Eric for excellent work and customer service.
Billy and Eric did a great job at identifying the issue with our hvac system and came very early in the time window given (huge convenience). Overall a great experience.
Billy was very thorough and explained in detail.
Trane equipment cooling maintenance
Replaced fan motor
Goodman ac cooling maintenance
Thermpride A/C replaced condenser fan motor and cycled system working at this time
Rheem A/C completed cooling maintenance and cycled system working at this time
Air ease gas pack checked system found bad igniton contral board and ignitor need to replace both
Bryant A/C checked system found to be low in refrigerate and added 1 lb R-410 refrigerate and cycled system working at this time
Goodman A/C added 1 lb R-22 refrigerate to system and cycled system working at this time
Trane gas furnace replaced contral board and cycled system working at this time
Trane heat pump and air handler checked system found blown low voltage fuse and replaced amd found no power to heat pump due to tripped breaker in main pannel box and main pannel bax was not accable
Thermopride A/C checked system found bad condenser fan motor need to replace fan motor
Trane gas furnace checked system found blower motor not running due to bad contral board need to replace contral board
Goodman gas furnace nad stright A/C checked both systems amd found to be working properly at this time
Trane gas pack replaced blpwer qheel and cycled system working at this time
Goodman A/C completed EPA cooling maintenance and cycled system working at this time