Billy was great and a pleasure to work with.
I really appreciated that the technician took the time to explain what was wrong and the options.
Explained to Kenny the situation what was going on, he listened to me and was very confident how he was going to resolve the problem.
Mr. Johnson was very knowledgeable
First of Billy was on time and ready to assest the problem he listen to my concerns and a check of the equipment and he agreed that it was thermostat as well he took care of it he was in and out in less than 30 to 45 min tops. You rock Billy😉 PS Billy was very respectful and professional which is always a plus
Worked on Trane air conditioner
We installed a 2 ton rheem straight ac and coil with new t6 tstat
Worked on Comfortmaker air conditioner
Worked on Lennox air conditioner
Comfortmaker heat pump,added 2 pounds r22 an can of leak seal
Lennox upstairs furnace had bad capacitor on blower motor changed out an checked downstairs Lennox systems are operating properly
Adjusted manual dampers and rewired t-stat.
Working on a low voltage short on a Comfortmaker gas furnace a zone system
Had a bee nest in flue causing restriction in air flow for the inducer motor thus causing pressure switch to open circuit cutting his Furnace out
Installed new furnace control board on a Comfortmaker gas furnace
Manual Jay load calculation and give an estimate to replace air conditioner and gas furnace.
Work on gas furnace
Cleaned flame sensor
Work on air conditioner
Worked on air conditioner