Billy was very knowledgeable. I felt he was thorough and trustworthy. Great attitude! All around nice guy.
Bill was very helpful with helping us upgrade our outdated hvac system. He listened to my concerns and found us a unit that was more energy efficient and cost effective. Thanks for all your hard work.
Billy was so helpful. A previous company came out 3 times and reported no problems with our a/c unit after having to put 2 pounds of Freon in. Billy listened to me regarding what was happening with the system and went straight to work to locate the leak in the system. He took pictures of where the leak was in order to help better explain the problem. He talked through all of our options and set up for a project manager to come to our home today.
Amana heatpump no cooling
Carrier package unit no cooling
Goodman heat pump completed cooling maintenance and cycled system working at this time
American Standard cooling maintenance
Carrier equipment cooling maintenance
Trane heat pump checked system found to be low in refrigerate and preferred leak search and found leaking evap coil need to replace coil
Aprilair humidifier replaced stem hose and cycled system working
ICO package heat pump replaced outdoor temp sencer and cycled system working at this time
Package heat pump no heat
Payne heatpump replaced txv
Payne package unit bad TXV
Worked on Goodman gas furnace
Worked on Carrier gas furnace
Worked on Goodman air conditioner