Goodman package heat pump completed cooling maintenance and cycled system working at this time
Carrier AC 2nd floor approximately a pound and a half low R22
Worked on Carrier 2zone system. Great Homeowner.check over system.filters clean.System operating normal at this time.
Amana heat pump second floor 35 5 dual capacitor blown in the outdoor unit replace cycled
20 year old Tempstar 1 lb low-22
Changed compressor in heat pump, 55 degree air comimgmout vents now.
First floor Goodman heat pump compressor shorted
Trane heat pump package unit cooling maintenance
Westinghouse gas pack replace high limit switch
Trane pac...no heat
York H/p...burning smell.........geatstrip
Goodman hp.....fan wires caught in blade
Trane heatpump bad 35/5dual capacitor