Best price of the three companies that bidder. Joel W. and crew were punctual, customer friendly and professional. Joel communicated very well and addressed all questions asked. I am very happy with the services received.
Install 20 kw Briggs and Stratton Fortress generator
Complete two systems. Preformed heating maintenance and found no mechanical issues with either system. Systems are heating properly at this time.
No ac....drains clogged
Ge mini split no cooling
Tempstar compressor failed
Carrier ac not cooling
Amana no cooling
Amana ac cooling maintenance
Goodman equipment......2nd no ac
Carrier split straight a.c. with gas furnace. Replaced bad condenser fan motor and dual capacitor Checked system for proper operation
Trane split a.c. with gas furnace. Replaced leaking slab coil and recharged system
Goodman split heat pump Diagnosed shorted condenser fan motor
Carrier split heatpump found bad condenser fan motor