AC repair job was expedited in a timely manner
Wholesome Company with Expertly trained and Kind service providers.
Professional as always me and my family thank you all for your services Bradley McLeod
Working on an Amana heat pump
Replaced an evaporator coil on an Amana heat pump
Routine maintenance on an Mitsubishi mini split
Routine maintenance on an Amana heat pump
Hail package heat pump checked system found hrar strips running with A/C due to wiring issue and corrected and cycled system working at this time
Goodman split heat pump cooling maintenance
Incomplete: 1System York split HP: HO said stopped cooling like last time. At the HP found system not running. Had 24v coming in but contactor not pulled in. Hooked gauges up and had 150psi on both sides. Checked power going into my board and I had it but not coming out. I str8 wired it to check board status. Bad board. I left unit bypassed so HO would have AC. Need new board from Virginia Air. Order in the AM.
Complete: 4 System: EPA Maintenances Heil Split Heat Pump/ Gas Furnace Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time. 3 mini split units with 5 Heads Checked Amp draws on compressor and blower, checked amp draws on fan. Cleaned units of spider webs, washed coils and filters. Systems are working as they should at this time. $0 Collected
Complete: 1System Goodman split HP: Came to install new Evap coil. Pumped unit down. Changed out old one brazed in new one. Nitro leak tested. Pulled vacuum 577. Released refrigerant added 4lbs of 410a. Had a SH of 29 and a SC of 15. Temp split was 20 degrees. System is working great at this time.
Goodman split Heat PUMP leaking Evaporator coil holds 17lbs of 410a refrigerant.
Complete: 1 System: EPA Maintenance Kenmore Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, blew out condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Complete: 1System: Kenmore split Hp Came to replace blower control board. Replaced board and system came on fine checked charge and system needed 1lb of 22 system is running great at this time.
Working on a York heat pump