Complete: 1 System: EPA Maintenance Heil Package unit : Air Handler: Checked Amp Draws on the Blower Motor and Heat strips and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Working on a Trane heat pump
Complete: Came to change out Heat Kit on DS unit. Removed old kit and rewired in new kit. They came on once the power was on. Cycled them off and on. System looks good and running great at this time.
Complete: 1 System: York Split HP: HO said was fine for the summer got back four days ago and wasn’t AC wasn’t cooling. I checked charge and was extremely low. Performed leak search. At AH found nothing. Opened top of condenser and could see oil in the bottom and noticed suction line and liquid line rubbing and found leak there. Cut out section of liquid line and repaired and brazed back together. Pressurized with nitrogen and Pulled Vacuum. No leaks. Added 8lbs of r22. Checked Delta T. System looks good and running great at this time.
performed preventive maintenance on Amana heat pump AC
Heating maintenance on Bryant gas furnace
Heating maintenance on heil package heat pump
4 ton heat pump replacement
Preventive maintenance on a heil heat pump