Technician knowledgable, courteous, and capable.
The guys spent time figuring out what was wrong rather than making an assumption and possibly a temporary fix
Both Billy and Cody were very professional and courteous. Informed me of my options and are ordering the part I need.
Goodman case coil repaired leak on liquid line near case coil and pulled vacuum and recharged system with R-22 refrigerant
Repaired a Goodman heat pump by replacing the evaporator coil and recharged system
Replace second floor evaporator coil Goodman unit
Repaired a Goodman heat pump by replacing the compressor
Trane A/C checked system found condenser fan motor not running due to bad dual run capacitor and replaced
Worked on ICP air conditioner- low on refrigerant -coil frozen solid
Second floor Trane AC insufficient cooling
Trane ac...2nd floor leaking valve stem
Trane AC replace condenser fan motor second floor
Trane AC 2 lb slow R22
Goodman gas pack checked system found compressor not running due to burnt wire on compressor and repaired and cycled system working at this time
Trane equipment drain stopped