Excellent service, as always, from a Comfort First.
Complete 1 System Amana HP Split System. EPA Cooling Maintenance. Checked tstat and replaced air filter. Checked blower amp draw. Inspected all wiring at the AH. Inspected evap coil. Drain line found clear. Checked compressor and cfm amp draws. Checked pressures. Inspected all wiring at the condenser unit. Cleaned condenser coil. System is running great at this time. Talked to HO about Installing a Surge Protector, HO stated she will be talking to her husban about it.
Amanna heat pump checked system found blown fuse and replaced and cycled system working at this time
Complete 1 System Amana HO Split System. HO stated system was not coming on. Checked air filter. Cycled system. Found drain line stopped up. Replaced P trap and made sure drain line was clear. Checked pressures. System is running great at this time.
Goodman split system Heat Pump
Work on Amana heat pump