Andy Steed did a great job in getting my ac back in order after 3 weeks without. He stuck with the problem until he found the solution. Can't say enough great things about him. However, the company as a whole fell down on the job and that's why I was without ac for so long. One mistake on top of another.
Carl quickly diagnosed what the problem was with our heat pump and repaired it.
Check unit found drain broke in wall/ electrical issues
Replaced txv on Trane Heatpump ,
Replace blown fuses chemically clean condenser coil system is running properly now
Replaced blower motor on York heat pump
We installed a 3 ton lennox heat pump and air handler with ten kw heat kit
Cleared primary condensate drain
Replaced 30 amp squared D breaker in sub panel. Checked operation. System working at this time.
Working on Rheem split heat pump Replace warranty low pressure switch and defrost board. Test operation and check all pressures and temps. System is working as it should at this time.
Ruud heat pump fpund to be low in refrigerant and added 2 lb R-410
Trane heat pump found compressor pulling high amps due to bad dual run capacitor and replaced and cycled system working at this time
Amana heat pump found bad control board and replace and cycled system working at this time
Arrived to work on split trane heat pump. Found indoor blower issue, caused by a bad fan relay. Replace fan relay and test operation. System working at this time.