Incomplete 2 Systems worked on US Trane HP 2 Zones. Ho stated system was not working. Checked and made sure zone dampers were working properly. Found cfm running but not compressor. Hard stark kit for trane is bad. It needs to be replaced. Used a hard start kit from truck stock temporarly until we get the one from trane. Will need to order from D&L. Condenser Data: M#: 4TWR4030D1000AA. S#: 15224KON4F.