Complete: 1System Amana Split HP: HO said the OD system would come on intermittently. Found no power from Y wire. The float switch had it turned off. Stopped up Trap. Replaced Ptrap and reset system. Due to the HO being an EPA customer I did not charge him for the repair to the Ptrap. When we come to do the maintenance we will not have to do that part.