Kenny has serviced one of our units before and I was very happy to see it was him that came to check why our air wasn't working today. He's very friendly and efficient!!
We installed a 4 ton 20 seer split heat pump system
Replaced the failed blower motor control board and 10kw strip heat. System is now cooling properly at this time.
Replaced a failed 35/5uf run capacitor. Upstairs ac is now running and working properly at this time.
Replaced downstairs run cap 35/5uf. System cooling fine.
Found outdoor unit running found compressor shorted to ground