Billy has been our tech for the last 3 visits and always gives us peace of mind that our HVAC is working as it should and answers any questions we have
He was very knowledgeable. Very kind. Gave me great advice and the house is warming up quick.
Billy was my technician He is a great people person
Josh the appointment scheduler was amazing and listened to my concerns. Very accommodating service. Billy the contractor who was assigned to fix the problem was very knowledgeable and kind. Great service and made sure we understood the work he completed. Thanks Billy & Josh.
Billy provided us excellent service during his visit. We had several questions regarding the issues with our unit, and Billy was very informative and did a great job explaining the issues and making sure we understood what our options were in terms of solutions to the problem. He explained everything simply, and I feel he provided everything I need to make an informed decision on repairing vs replacing. Thank you Billy!
Billy was great! He was very thorough in his explanation and explained everything well. His customer service was amazing
In and out in no time got the furnace fixed
Was able to fit me in on their schedule during a very busy time. The service tech was accommodative and knowledgeable.
Very pleased with tech and his service. Disappointed in length of time from initial call July 13 and system running again on July 25.
Estimate for new heating and cooling system
Complete 2 Systems worked on US Trane Straight A/C System. HO stated blower motor would run and stop, run and stop running. Found blower motor overheating and overamping. Run cap was fine. Replaced blower motor. Used a 1/2 HP 120V blower motor, a motor bracket, and a 10 uf run cap from truck stock. Cycled system. Checked pressures. System is running great at this time.
Complete 1 System Bryant Syraight A/C Pak System System: EPA Cooling Maintenance. Checked tstat and air filter. Checked blower motor amp draw and run cap. Inspected all wiring at the AH. Inspected evap coil. Drain line found clear. Checked compressor and cfm amp draws. Checked pressures. Inspected all wiring at the condenser unit. Checked dual cap. Cleaned condenser coil. System is running great at this time.
Trane hp 2bls r22
Complete 1 System Payne Gas Pak. Came to complete job. Came to replace flue cover. Had to remove inducer, gas valve electrical panel. Installed new flue cover. Installed back every thing else. Cycled system. Let HO know she would have to leave door open for a few mins due to first start on new heat exchanger would creat some smoke. Ran system for a few mins. System is running great st this time.
Worked on Trane gas furnace
Complete 2 Systems worked on US Trane Gas Furnace. HO stated system stopped working. Found tstst not sending signal to system. Checked and made sure no broken wires were found. Replaced tstat. Used a proselect prog tstat from truck stock. Cycled system. System is running great at this time.
Trane hp heating maintenance
Incomplete 1 System. Couldnt performe AHS heating Maintenace. We will need a 10’ ladder to go up in the attic. 10’ ladder to reach gas furnace.
Trame A/C checked system found nest thermostat not controlling system due to being bad and replaced with truck stock thermostat and cycled system working at this time
Carrier replaced zone damper mootr and cycled system working at this time
Amanna heat pump checked system found bad condensation pump and replaced and cycled system working at this time
Trane gas furnace checked system found bad blower motor and replaced with truck stock motor and cycled system working at this time
Carrier A/C checked system found no air flow to second floor due to zone damper not oping cased by bad zone damper motor need to replace zone damper motor
Goodman A/C reclaimed refrigerate replaced compressor bi flow drier capacitor and pulled vacuum and recharged system with 6 lb refrigerate and cycled system working at this time