Billy has been our tech for the last 3 visits and always gives us peace of mind that our HVAC is working as it should and answers any questions we have
He was very knowledgeable. Very kind. Gave me great advice and the house is warming up quick.
Billy was my technician He is a great people person
Josh the appointment scheduler was amazing and listened to my concerns. Very accommodating service. Billy the contractor who was assigned to fix the problem was very knowledgeable and kind. Great service and made sure we understood the work he completed. Thanks Billy & Josh.
Billy provided us excellent service during his visit. We had several questions regarding the issues with our unit, and Billy was very informative and did a great job explaining the issues and making sure we understood what our options were in terms of solutions to the problem. He explained everything simply, and I feel he provided everything I need to make an informed decision on repairing vs replacing. Thank you Billy!
Billy was great! He was very thorough in his explanation and explained everything well. His customer service was amazing
In and out in no time got the furnace fixed
Was able to fit me in on their schedule during a very busy time. The service tech was accommodative and knowledgeable.
Very pleased with tech and his service. Disappointed in length of time from initial call July 13 and system running again on July 25.
Trame A/C checked system found nest thermostat not controlling system due to being bad and replaced with truck stock thermostat and cycled system working at this time
Carrier replaced zone damper mootr and cycled system working at this time
Amanna heat pump checked system found bad condensation pump and replaced and cycled system working at this time
Trane gas furnace checked system found bad blower motor and replaced with truck stock motor and cycled system working at this time
Carrier A/C checked system found no air flow to second floor due to zone damper not oping cased by bad zone damper motor need to replace zone damper motor
Goodman A/C reclaimed refrigerate replaced compressor bi flow drier capacitor and pulled vacuum and recharged system with 6 lb refrigerate and cycled system working at this time
Goodman heat pump checked system found to be running in heat mode due to lose qorong connection in reversing valve qire and repaired amd cycled system working at this time
Goodman hp...insufficient cooling
Trane ac....no cooling
Lennox heat pump completed EPA cooling maintenance and cycled system working at this time
No ac.bad blower motor
Rheem....hp frozen unit
Complete 1 System Coleman Straight A/C System. Came to perform AHS cooling Maintenance. Checked thermostat and air filters. Checked blower motor amp draws. Checked all wiring. Inspected evap coil and blower wheel. Checked run cap. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Rinsed condenser coil. Checked pressures. Also HO would like to get a quote for installing one more vent in one of the rooms US, beacuase she said she feels existing vent is not. blowing enough air. I checked damper and it’s fully open. System is running great at this time.
Carrier hp...bad indoor txv