Billy has been our tech for the last 3 visits and always gives us peace of mind that our HVAC is working as it should and answers any questions we have
He was very knowledgeable. Very kind. Gave me great advice and the house is warming up quick.
Billy was my technician He is a great people person
Josh the appointment scheduler was amazing and listened to my concerns. Very accommodating service. Billy the contractor who was assigned to fix the problem was very knowledgeable and kind. Great service and made sure we understood the work he completed. Thanks Billy & Josh.
Billy provided us excellent service during his visit. We had several questions regarding the issues with our unit, and Billy was very informative and did a great job explaining the issues and making sure we understood what our options were in terms of solutions to the problem. He explained everything simply, and I feel he provided everything I need to make an informed decision on repairing vs replacing. Thank you Billy!
Billy was great! He was very thorough in his explanation and explained everything well. His customer service was amazing
In and out in no time got the furnace fixed
Was able to fit me in on their schedule during a very busy time. The service tech was accommodative and knowledgeable.
Very pleased with tech and his service. Disappointed in length of time from initial call July 13 and system running again on July 25.
Trane ac....no cooling
Lennox heat pump completed EPA cooling maintenance and cycled system working at this time
No ac.bad blower motor
Rheem....hp frozen unit
Complete 1 System Coleman Straight A/C System. Came to perform AHS cooling Maintenance. Checked thermostat and air filters. Checked blower motor amp draws. Checked all wiring. Inspected evap coil and blower wheel. Checked run cap. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Rinsed condenser coil. Checked pressures. Also HO would like to get a quote for installing one more vent in one of the rooms US, beacuase she said she feels existing vent is not. blowing enough air. I checked damper and it’s fully open. System is running great at this time.
Carrier hp...bad indoor txv
Worked on Armstrong gas furnace
Worked on Lennox gas furnace
Worked on Armstrong gas pack
Trane split system Heat Pump cooling maintenance
Colman cooling maintenance
Worked on York heat pump
Worked on Trane heat pump
Worked on York gas furnace