Was able to fit me in on their schedule during a very busy time. The service tech was accommodative and knowledgeable.
Very pleased with tech and his service. Disappointed in length of time from initial call July 13 and system running again on July 25.
Changed condensate Pump
Check Armstrong heat pump -found bad reversing valve-ordering new part
Checked American Standard unit-found bad compressor/it under warranty preferred new-
Trane ac...door iff to furnace
Replaced a compressor on a Carrier
Goodman pack...1bl low r22
Repaired a Lennox heat pump by replacing the evaporator coil and recharged system
Linux heat pump air handler evaporator coil leaking
Goodman heat pukp and air handler checked system found bay pass vamp not working properly and repaired and cycled system working at this time
LG mini split possible wheel vibrating creating loud noise
LG mini split
Goodman equipment intermittent
Goodman heat pump frozzen up need to reschedule when system has de iced