In and out in no time got the furnace fixed
Was able to fit me in on their schedule during a very busy time. The service tech was accommodative and knowledgeable.
Very pleased with tech and his service. Disappointed in length of time from initial call July 13 and system running again on July 25.
Heil package unit loose wire
Goodman gas pack checked system found compressor and condenser fan motor not running due to bad dual run capacitor and replaced with 30/5 capacitor and cycled system working at this time
Trane ac checked system found to be low in refrigerant and added 1 on R-22 to system and cycled system
Replace condenser fan motor Comfortmaker unit
Trane coil. ... Frozen
Changed condensate Pump
Check Armstrong heat pump -found bad reversing valve-ordering new part
Checked American Standard unit-found bad compressor/it under warranty preferred new-
Trane ac...door iff to furnace
Replaced a compressor on a Carrier
Goodman pack...1bl low r22
Repaired a Lennox heat pump by replacing the evaporator coil and recharged system
Linux heat pump air handler evaporator coil leaking