Amana gas pack check
Complete one system. Found blown 45/5 dual capacitor and replaced it. System is operating properly at this time.
Blown 45/5 capacitor
Goodman hp 2bls low r410
Goodman hp....low charge
Intertherm mobile home unit bad fan relay
Trane gas furnace replaced blower motor and rechecked humidifier and cycled system working at this time
Goodman gas furnace cleaned out flue pipe . Cycled system
Installed whole house filter and April air humidifier.
Complete: 1 System: Goodman Gas Package: EPA Maintenance: Checked the Amp Draws on the blower motor, fan and condenser. Checked the capacitor. Checked Charge and Tstat and filters. Checked Heat Exchanger. Cleaned burners, Flame sensor and Checked Roll out switch. Cleaned unit out. System looks good and working good at this time.
Amana heat pump package unit Frozen
Complete: 2 Systems worked on downstairs unit: Goodman Split HP/ Rheem AH. HO complaining about water buildup in AH. Condensate line was completely clogged. AH is very old. And has rust all around pvc fitting going into metal Evap. Informed HO when that piece fails getting a new part will virtually be impossible and gave him the information on what will happen at that point. But right now system is operating as it should in heat mode. I did blow out line and replaced Ptrap.
Intertherm replaced heat strips ,sequencers rewired low and high voltage
Goodman Heat Pump