Guys did a great job
Goodman gas furnace cleaned out flue pipe . Cycled system
Installed whole house filter and April air humidifier.
Complete: 1 System: Goodman Gas Package: EPA Maintenance: Checked the Amp Draws on the blower motor, fan and condenser. Checked the capacitor. Checked Charge and Tstat and filters. Checked Heat Exchanger. Cleaned burners, Flame sensor and Checked Roll out switch. Cleaned unit out. System looks good and working good at this time.
Amana heat pump package unit Frozen
Complete: 2 Systems worked on downstairs unit: Goodman Split HP/ Rheem AH. HO complaining about water buildup in AH. Condensate line was completely clogged. AH is very old. And has rust all around pvc fitting going into metal Evap. Informed HO when that piece fails getting a new part will virtually be impossible and gave him the information on what will happen at that point. But right now system is operating as it should in heat mode. I did blow out line and replaced Ptrap.
Intertherm replaced heat strips ,sequencers rewired low and high voltage
Goodman Heat Pump
Trane split hp found high and low voltage short
Working on a Trane heat pump
Working with customer to design a new whole house Comfort System.
Goodman dual fuel heat pump with gas furnace corrected burnt wires bad capacitor and poorly running gas furnace
Cooling maintenance on 2 trane heat pumps
Goodman dual dual package system not starting due to bad draft inducer motor need to replace draft inducer assimbly
Goodman hp...low charge bad 40/5 capacitor