why copper tubing cast was tagged on, that should have been part ob the install equipment process/work order. But for Soldering the copper tubes No modifications were done.
Tempstar gas furnace and Amanna gas pack completed EPA heating maintenance and cycled system working at this time
Complete 1 System 3 Zones Lennox Straight A/C: Came to replace motor damper for 3rd Floor. Tested it. System is properly working.
Carrier gas furnace found bad cfm
Lennox gas furnace found bad capacitor
Rheem gas pack checked system found compressor not starting due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Carrier A/C completed cooling maintenance and cycled system working at this time
Lennox A/C checked system found bad zone damper motor need ro replace zone damper motor
Trane Heat pump replaced indoor 5XV and bi flow drier and cycled system working at this time
Complete 2 Systems worked on US Carrier Straight A/C: replaced case coil. Recovered ref. Removed old case coil. Installed new one in. Replaced p trap, and made sure drain line was clear. Leak tested system. Pulled vacuum. Added 9 lbs of 410A. Checked pressures. System is running great at this time.
Amana gas pack performed cooling maintenance
Lennox equipment noise
Complete 2 Systems worked on US Carrier Straight A/C: HO stated system was not cooling. Found system low in ref. Added 2 lbs of 410A. Added a can of leak stop. System is running great at this time.
Complete 2 Systems worked on DS Goodman A/C: HO said system ds was not cooling. Found way too dirty air filter. Removed it. HO getting new one later on. Found a burnt wire at condenser, the common wire going from contactor to dual cap common side. Repired wire. Checked pressures. System is running great at this time.