Cooling maintenance on Lennox gadpack
2 unit cooling maintenance
Found unit low on r22 by 1lb causing unit to freeze up. Added 1 on and now 59 degree air out vents.
Replaced capacitor on trane ac
Replaced secondary drain pan
Charged system with 5 lbs of 410. 55 degree air out vents.
Changed outdoor fan motor
Changed condenser motor
Changed compressor on upstairs a.c.. 56 degree air coming out vents now.
Changed main drain pan on downstairs heat pump
Replaced gas metal exhaust elbow
Changed case cpil, now have 58 degree air out vents.
Working with customer to replace upstairs and downstairs air conditioner and furnace with high efficiency 18 Seer systems.
Lennox gas furnace replaced draft inducer assembly and pressure switch and cycled system working at this time
Providing an estimate for customer to replace split heat pump