why copper tubing cast was tagged on, that should have been part ob the install equipment process/work order. But for Soldering the copper tubes No modifications were done.
Lennox equipment not heating
Lennox equipment cooling maintenance
Lennox equipment heating maintenance
Lennox gas furnace
Goodman gas pack ,Replaced furnace control board , programmed eco bee and tested heating and cooling
Complete maintenance on Payne gas furnace and carrier gas furnace
Complete 1 System Goodman HP Split System: completed EPA Heating Maintenance. Sprayed coil cleaner to condenser and wash it out. System is running great at this time.
Tempstar gas furnace and Amanna gas pack completed EPA heating maintenance and cycled system working at this time
Complete 1 System 3 Zones Lennox Straight A/C: Came to replace motor damper for 3rd Floor. Tested it. System is properly working.
Carrier gas furnace found bad cfm
Lennox gas furnace found bad capacitor
Rheem gas pack checked system found compressor not starting due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Carrier A/C completed cooling maintenance and cycled system working at this time
Lennox A/C checked system found bad zone damper motor need ro replace zone damper motor