why copper tubing cast was tagged on, that should have been part ob the install equipment process/work order. But for Soldering the copper tubes No modifications were done.
Lennox equipment noise
Complete 2 Systems worked on US Carrier Straight A/C: HO stated system was not cooling. Found system low in ref. Added 2 lbs of 410A. Added a can of leak stop. System is running great at this time.
Complete 2 Systems worked on DS Goodman A/C: HO said system ds was not cooling. Found way too dirty air filter. Removed it. HO getting new one later on. Found a burnt wire at condenser, the common wire going from contactor to dual cap common side. Repired wire. Checked pressures. System is running great at this time.
Lennox ac check
Goodman gas furnace performed cooling maintenance
Complete 1 System worked on Lennox HP Split System: Cooling Maintenance. Checked thermostat and air filters. Replaced Air filter provided by HO. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Rheem ac check
Lennox bad compressor
Goodman gas pack and /C completed cooling maintenance
Lennox air handler replaced zone damper motor and cycled system working at this time
Goodman A/C reclaimed refrigerate replaced compressor bi flow drier and recharged system with 9 lb R438A and cycled system working at this time
Working on a Goodman heat pump
Working on 2 Lennox heat pumps
Lennox gas furnace found bad ECM replaced 1075 hp 1/3
Goodman ac check