Worked on Goodman split system replaced 3ft low-voltage wiring Cycle System running properly
Worked on Goodman heat pump found condenser coil completely clogged chemically clean coil Cycle System running properly
System a little low on refrigerant added 1 lb system running properly
Worked on two systems found leak on Goodman package unit second system is working properly
Checked Goodman package unit found bad capacitor- fixed ductwork /small holes in flex duct
Installed evaporator coil in carrier ah
Found 2 ton Janitrol ac with bad capacitor. Replaced capacitor on sight and get system working as it should.
Found Goodman heat pump not working properly due to a faulty thermostat. Replace existing thermostat with Honeywell 3000. System working properly at this time.