Ryan is professional and checked the complete system for our home.
Complete one system, main heat pump. Found clogged primary drain and cleared it out. System is operating properly at this time.
Complete one main heat pump. Checked systems operations. System is operating properly at this time.
Complete two systems downstairs heat pump. Found bad breaker for the outside unit and replaced it. Found bad capacitor and replace it. System operating properly at this time.
Worked on Goodman split system replaced 3ft low-voltage wiring Cycle System running properly
Worked on Goodman heat pump found condenser coil completely clogged chemically clean coil Cycle System running properly
System a little low on refrigerant added 1 lb system running properly
Worked on two systems found leak on Goodman package unit second system is working properly
Checked Goodman package unit found bad capacitor- fixed ductwork /small holes in flex duct
Installed evaporator coil in carrier ah
Found 2 ton Janitrol ac with bad capacitor. Replaced capacitor on sight and get system working as it should.
Found Goodman heat pump not working properly due to a faulty thermostat. Replace existing thermostat with Honeywell 3000. System working properly at this time.