Complete 2 Systems Amana HP Split Systems Performed EPA Heating Maintenance US Amana HP Slit System: Checked thermostat and air filter. Checked amp draws on heat strips and blower motor. Checked run cap. Inspected evap coil. Made sure drain line was clear. Checked compressor and cfm amp draws. Tested defrost board. Checked dual cap. Checked pressures. Cleaned condenser coil. System is running great at this time. DS Amana HP Split System. Performed EPA Heating Maintenance Checked thermostat and air filter. Checked amp draws on heat strips and blower motor. Inspected evap coil. Made sure drain line was clear. Checked compressor and cfm amp draws. Tested defrost board. Checked dual cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Incomplete: Recall: HO said unit with Compressor we installed suddenly started tripping breaker. Ohmed Compressor and It was giving me 14.9,14.9 and 1.5. Unplugged compressor and fan came on. Bad compressor. Need to call in the morning to get new compressor info. Unit Holds 7lbs of 438a
Incomplete: 2 systems worked on both units. US Trane System Str8 A/C Gas Furnace: HO wanted us to check both heating and cooling. Checked A/c First and was 1lb low in refrigerant and had dirty filter. Replaced filter and Charged with r22 and system is working great. Checked US Gas Furnace. It immediately came on and I cycled it a couple times with no issues. HO said once it started heating it was great but when u first turned it on it wouldn’t blow warm air. Explained having to get cool air out of ducts first. System is working great at this time. DS Trane Gas Package Unit: HO wanted us to check heat and cool. Checked heat. Found gas valve not opening up. Need to order new gas valve. Checked gas valves on truck and did not have a match. Then checked AC and all looked great at this time.
EPA maintenance on 2 Amana heat pumps
Complete: Trane Split HP: Fan would not turn. Checked cap and it was bad. 60/5 ...... only had a 60/10 so I used the 60 side and wired in a 5 cap. System came on, checked temps and working good at this time.
Nordyne air handler bad run capacitor
Trane air handle checked the games blower not coming on due to bad blower relay and replaced and cycled system working at this time
Heat maintenance on an Amana heat pump
Heat maintenance on a Goodman heat pump
Reprogrammed zone board on a Goodman gas system
Found a bad heat exchanger on a carrier gas pack
Trane heat pump checked system found compressor not starting due to bad run capacitor and replaced and cycled system working at this time