Complete: Trane Split HP: Fan would not turn. Checked cap and it was bad. 60/5 ...... only had a 60/10 so I used the 60 side and wired in a 5 cap. System came on, checked temps and working good at this time.
Nordyne air handler bad run capacitor
Trane air handle checked the games blower not coming on due to bad blower relay and replaced and cycled system working at this time
Heat maintenance on an Amana heat pump
Heat maintenance on a Goodman heat pump
Reprogrammed zone board on a Goodman gas system
Found a bad heat exchanger on a carrier gas pack
Trane heat pump checked system found compressor not starting due to bad run capacitor and replaced and cycled system working at this time