Incomplete 3 Systems worked on Main Floor Unit and Basement Unit. Main Floor System, Goodman Straight A/C: HO stated system was not cooling. Found Drain line stopped up. Replaced P trap and cleared line. Found system charge low. Added 1 lbs of R22. System is running great at this time. Basement Goodman Straight A/C, M#: GSC130181AE. S#: 0706039509. Case Coil Data: M#: CAPF1824A6AA. S#: 0706598348. HO stated system was not cooling. Found breaker tripped. Checked comp windings. They are bad. Comp needs to be replaced. Called Arco to get part info. P#: AR16. Price: $278.48. In Stock. System holds 7 lbs of R22. Did not order due to HO requesting info towards a new system.