The service technician presented himself very professionally. He was punctual and informative, giving me a clean understanding that my system was/ is ready for another hot summer and more importantly that comfort first heating and cooling will be there should a situation arise. One reason we continue with your organization is the peace of mind due to the communication and honesty of BJ Thank you. Lisa Chagnon
Mr McCleod came to our house for a bi-annual inspection. He is professional in presentation and provides a complete service. When he leaves I have confidence my unit is in good working repair. In short Bradley is the main reason we work with your company. It’s about trust and value
Installing a new thermostat for an Amana heat pump
Repairing a drain line on an Amana heat pump
Working on a Trane heat pump
Working on a Carrier heat pump
Complete: 2 systems worked on DS System: HO was a little concerned about how cool is crawl space was. So I checked all duct work which is in fairly decent shape. He had very minimal leaking around supply lines off trunk. Did find several small holes in his duct board supply line. Patched holes and all seems to be good at this time.
Working on a Goodman heat pump
Complete 1 System EPA maintenance on a Bosch Heat Pump Split System checked amp draws on condenser fan, compressor and blower motor. Checked refrigerant charge on unit. Cleaned condenser coil. Checked all wiring at condenser and air handler. Replaced P trap. System running great at this time.
Working on a Sanyo mini split
Complete: 1 System: Bosch Split HP: EPA Maintenance: Bosch Split HP: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.