Complete 1 System Amana Straight A/C System. Performed EPA Cooling Maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Checked run cap. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Found it very weak. It was down more than 50% off capacity. Replaced it with a 45/5 dual cap from truck stock. Dual cap is under 10 years parts and labor warranty. Checked pressures. Cleaned condenser coil. System is running great at this time.