Incomplete 1 System (brand name N/A) Straight A/C: came to do cooling maintenance. Checked tstat and air filter. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Checked run cap. Found drain line broken. Drain line needs repair. Will need 1/2” pvc pipe fittings. 1 elbow, 2 couplings, 1 p trap, 1 12” pvc pipe, 1 t, and 1 cap., checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. Charged Level 2 to HO for the drain repair. System is running great at this time.