Bill was very knowledgeable and helped walk us through different options. I would definitely recommend consulting with comfort First.
Excellent service. Very friendly and professional. Showed up on schedule. Evaluate the problem and had us back up and running in a matter of minutes.
On time. Thorough and explained the repair
Prompt, courteous and efficient. He was an extremely nice guy as a bonus!
Bill was great and took the time to explain the issues with my air unit. He was very knowledgeable and I felt like he was offering me the best price they could do- he presented multiple options and talked through these options with the benefits or each. Would definitely recommend him!
Very professional and courteous. Very helpful and honest.
From sales, to finance to installation Comfort First is a class act. They had me scheduled within a week for the installation. Andy Steed was extremely professional, knowledgeable and efficient. After the install, he followed up to make sure everything was working properly. I can't thank them enough for saving me this summer! I would highly recommend Comfort First to anyone who wants a professional and stress-free experience!
Very professional and timely.
Bill was and is amazing! Bill was honest, extremely professional, responded quickly and he was knowledgeable about all the products he shared. He made the process very easy and helped me choose the best unit for me. I will definitely recommend Comfort First in the future! Thank you!
Complete one system, Lennox Gas Furnace. Found pan full of water and repiped condensate line. Found system low in refrigerant and added 1 lb of r22. System is operating properly at this time.
Complete: 1System Lennox Gas Furnace Str8 AC: HO said it just stopped blowing air on Sunday night. At the AH found pan full of water. Repiped condensate line and checked charge. Charge was down 1lb of 22. Added the lb and delta T was 18°. System working great at this time.
Complete two systems, upper split heat pump. Found bad dual capacitor and hard start and replaced both. Found unit low in refrigerant and added 1 lbs of r22. System is operating properly at this time.
Carrier water in drain pan
Complete three systems, bonus room above garage. Found compressor and CFM not running due to bad contactor and replaced it. System is operating properly at this time.
Carrier ac...compressor is failing
York ac check
Carrier ac not cooling
Carrier gaspack evap/coil leakin
Quote for new hvac system
Lennox split straight a.c. with gas furnace. Diagnosed bad dual cap. Replaced with new and checked system for proper operation
Goodman ac check
Nordyne split straight a.c. with gas furnace. Replaced bad condenser fan motor with new and checked system for proper operation
Complete one repair, Trane split heat pump, downstairs closet. Found compressor not running due to burnt wire on hard start kit and replaced it. System is operating properly at this time.
Complete one system, split a/c with gas furnace. Found low voltage short at condenser on the t-stat wire and repaired it. System is operating properly at this time.