Service visit to correct a minor issue with the original inspection. Joshua did a great job to resolve the issue and even adjusted another issue not identified during the original inspection. Great customer service and more than willing to answer any questions.
Honesty goes a long way in the service industry, you can trust these guys.
He was well groomed, handsome, very polite and placed on shoe protectors upon entry of home. Explained everything and was quick to diagnose problem.
Super nice. Came in, did what needed to be done and was out.
The technicians were professionals. Very Courteous!
This is my first time using this company and the first thing I noticed was the great customer service when I called to schedule an appointment. I received a courtesy call letting me know he was on the way to my home. Billy was very polite, exhibited great customer service skills, and was very knowledgeable. I highly recommend Comfort First Heating and Cooling and will use them in the future.
Lennox gas furnace found bad capacitor
Complete 1 System Goodman Straight A/C: HO said system was not cooling. Found bad dual cap. Used a 45/5 cap. Checked pressures. System is running great at this time.
Incomplete 2 Systems worked on DS Carrier HP Split System. Recovered ref. Came to replace reversing valve. Removed old one. Installed new one in. Leak tested system. Pulled vacuum. Added 6 lbs of 438A. Used 2 lbs from new jog. 4 lbs from recoverey tank was as much as We could get out. Tested. Reversing valve was defective, checked reversing valve coil. Ohmmed it out. Made sure i was getting 24v. Tap reversing valve gently, still couldnt make it work. It needs to be replaced. Called Totalline to order new part. P#:EF17BZ113. Price: $174.30. In stock. Ready for pick up. PO#: 74610. Will need to recover ref in a new tank and reuse ref.
Fixed electrical box and drain
Trane straight ac found bad thermostat
Ruud gas furnace preformed cooling maintenance
Trane straight ac bad cfm
Carrier ac broken cfm blade
Comfortmaker intermitten fan issues
Lennox equipment replace zonedamper motor
Goodman A/C checked system found compressor not pumping due ti bad valves in compressor need to replace compressor
Lennoxe A/C checked system found dirty condenser coil and cleaned and found system to be low in refrigerate and added 2 lb R-22 to system and cycled system working at this time
Carrier hear pump replaced compressor and found reversing valve not shifting properly need to replace reversing valve
Trane gas furnace checked system found blower motor not running due to bad capacitor and replaced and cycled system working at this time
Change out ptac unit