This is my first time using this company and the first thing I noticed was the great customer service when I called to schedule an appointment. I received a courtesy call letting me know he was on the way to my home. Billy was very polite, exhibited great customer service skills, and was very knowledgeable. I highly recommend Comfort First Heating and Cooling and will use them in the future.
Thomas was friendly, professional, knowledgeable, efficient, and safety focused.
Bill was very knowledgeable and helped walk us through different options. I would definitely recommend consulting with comfort First.
Excellent service. Very friendly and professional. Showed up on schedule. Evaluate the problem and had us back up and running in a matter of minutes.
On time. Thorough and explained the repair
Prompt, courteous and efficient. He was an extremely nice guy as a bonus!
Bill was great and took the time to explain the issues with my air unit. He was very knowledgeable and I felt like he was offering me the best price they could do- he presented multiple options and talked through these options with the benefits or each. Would definitely recommend him!
Trane split heat pump. Set cut in and out to lower temperature
Trane split heat pump. Replaced bad contactor
Carrier gas furnace checked system found blown low voltage fuse and replaced and cycled system working at this time collected
Payne split heat pump. Diagnosed bad Wi-Fi thermostat
Lennox checked system found tripped breaker in main panel box due to bad dual run capacitor start relay and start capacitor
I'm split heat pump. Replaced faulty defrost coil sensor
Goodman gas furnace found inducer motor seized up
Goodman package heat pump checked system found bad defrost sencer need to replace
Goodman heat pump checked system not going into defrost cycle due to bad defrost thermostat and replaced and found to be low in refrigerate and added 1 lb R-410A and cycled system working at this time
Goodman gas furnace adjusted dampers in duct work for air flow
Goodman gas pack checked system found failed igniton contral board need to replace board
Bryant heat pump checked system found no power to heat pump due to tripped breaker 8n main panel reset breaker amd found bad breaker also found compressor pulling high start amps due to bad dual run capacitor and replaced
Trane gas pack preformed heating maintenance
Nordyne split heatpump replaced heat strips
Trane gaspack replaced inducer motor