The technicians were professionals. Very Courteous!
This is my first time using this company and the first thing I noticed was the great customer service when I called to schedule an appointment. I received a courtesy call letting me know he was on the way to my home. Billy was very polite, exhibited great customer service skills, and was very knowledgeable. I highly recommend Comfort First Heating and Cooling and will use them in the future.
Thomas was friendly, professional, knowledgeable, efficient, and safety focused.
Bill was very knowledgeable and helped walk us through different options. I would definitely recommend consulting with comfort First.
Excellent service. Very friendly and professional. Showed up on schedule. Evaluate the problem and had us back up and running in a matter of minutes.
On time. Thorough and explained the repair
2.tons amana heat pump
Carrier gas pack checked system found cracked heat exchanger need to replace heat exchanger
Incomplete 1 System Trane HP Split System HO stated system was not cooling. System is 30 years old. Found system extremely low in refrigerant. Performed a leak serach. Added 400 psi of nitrogen. Couldnt find the leak. Will need to add dye in system to find the leak. System holds 6 lbs of R22. Existing system at the AH is completely rusted out. Talked HO about getting a new system. He said he was interested on knowing his options towards a new system. Filled ip a lead sheet and sent it to beth. Ah data N/A. Condenser Data: M#: TW072B100A0. S#: D16254426.
Goodman cooling maintenance
Complete 2 Systems worked on US Goodman A/C: replaced case coil. Recovered ref. Removed old case coil. It took us 2 hrs and one half due to having to do modifications to coil, drain line and copper lines. Installed new case coil, taped it up. Installed return plenum back. Leak tested system. Pulled vacuum. Added refrigerant. It took 6 lbs of R22. System is running great at this time.
Goodman Gas Package
Rheem gas furnace performed cooling maintenance
Trane gas furnace replaced control board
Carrier split heatpump replaced control board
Mitsubishi mini split Diagnosed bad control board
Ruud Split system straight AC added refrigerant replaced contactor added hard start